## Capacitance

When a charge is delivered to a conductor its potential is raised in proportion to the quantity of charge given to it. At a particular potential a conductor can hold a given amount of charge. **Capacitance** is the term to indicate the limited ability to hold charge by a conductor.

Let charge given to a conductor be = **q**

Let **V** be the potential to which it is raised.

Then q α V, or

q = CV

**C** is constant for a **conductor** depending upon its shape size and surrounding medium. This constant is called capacitance of a conductor.

**V = 1 Volt**than

**C = Q**, thus capacitance is defined as the amount of electric charge in coulomb required to raise its potential by one volt.

If **V = 1 Volt** than **C = Q**, and **Q = 1 Coulomb** than **C = 1 Farad** thus one Farad is capacitance of a capacitor which stores a charge of one coulomb when a voltage of one volt is applied across its terminal.

## Capacitor

A capacitor or condenser is a device for storing large quantity of **electric charge**. Though the capacity of a conductor to hold charge at a particular potential is limited, it can be increased artificially. Thus any arrangement for increasing the capacity of a conductor artificially is called a capacitor.

- Capacitors are of many types depending upon its shape, like parallel plate, spherical and cylindrical capacitors etc….

- In capacitor there are two conductors with equal and opposite charge say
**+q**and**–q**. Thus q is called charge of capacitor and the potential difference is called potential of capacitor.

### Principle of Capacitor

Let **A** be the insulated conductor with a charge of **+q** units. In the absence of any other conductor near **A** charge on **A** is **+q** and its potential is **V**. The capacity of conductor **A** is therefore given by:

C = qV

If a second conductor B is kept closed to A than electrostatic induction takes place. **–q** units of charge are induced on nearer face of **B** and **+q** units of charge is induced on farther face of **B**. Since **B** is earthed the charge **+q** will be neutralized by the flow of electrons from the earth.

Potential of A due to self charge = **V**

Potential of A due to –q charge on B = **-V’**

Thus net potential of A = V + (-V’) = V -V’ which is less than **V**

Hence potential of **A** has been decreased keeping the charge on it fixed, hence capacitance has been increased.

With the presence of **B** the amount of work done in bringing a unit positive charge from infinity to conductor **A** decreases as there will be force of repulsion due to **A** and attraction due to **B**. Thus resultant force of repulsion is reduced on unit positive charge and consequently the amount of work doe is less and finally due to this potential of **A** decreases.

Therefore capacity of **A** to hold charge (* Capacitance*) is increased.

## Dielectric Strength

The material between the two conductors **A** and **B** as shown in figure above is always some **dielectric material**. Under normal operating conditions the dielectric materials have a very few free electrons. If the electric field strength between a pair of charged plates is gradually increases, some of the electrons may be detached from the dielectric resulting in a small current.

When the electric filed strength applied to a dielectric exceeds a critical value, the insulating properties of the dielectric material gets destroys and starts conducting between the two conductors **A** and **B**.

This is called breakdown of dielectric which is fault condition for a capacitor bank. The minimum potential gradient required to cause such a break down is called the dielectric strength of the material. It measures the ability of a dielectric to withstand breakdown. It is expressed as **kV/mm**.

It is reduced by moisture, high temperature; aging etc. Below table gives dielectric strength of some dielectrics.

Si.No. | Dielectric Material | Dielectric strength [kV/mm] |

1 | Air | 3 |

2 | Impregnated Paper | 4 – 10 |

3 | Paraffin Wax | 8 |

4 | Porcelain | 9 – 20 |

5 | Transformer Oil | 13.5 |

6 | Bakelite | 20 – 25 |

7 | Glass | 50 – 120 |

8 | Micanite | 30 |

9 | Mica | 40 – 150 |

Dielectric Strength for capacitor is the maximum peak voltage that the capacitor is rated to withstand at room temperature. Test by applying the specified multiple of rated voltage for one minute through a current limiting resistance of 100 Ω per volt.

## Sizing of Capacitor banks for power factor improvement

The Power Factor Correction of electrical loads is a problem common to all industrial companies. Every user which utilizes electrical power to obtain work in various forms continuously asks the mains to supply a certain quantity of active power together with reactive power.

**Most loads on an electrical distribution system can be placed in one of three categories:**- Resistive
- Inductive
- Capacitive

The most common of these on modern systems is the inductive load. Typical examples includes transformer, fluorescent lighting, AC induction motors, Arc/induction, furnaces etc. which draw not, only active power from the supply, but also inductive reactive power (KVAr). Common characteristics of these inductive loads is that they utilize a winding to produce an electromagnetic field which allows the motor or transformer to function and requires certain amount of electrical power in order to maintaining the field.

Therefore Active Power (KW) actually performs the work whereas Reactive Power (KVAr) sustains the electro-magnetic field. This reactive power though is necessary for the equipment to operate correctly but could be interpreted as an undesirable burden on the supply.

If we quantify power factor improvement aspect from the utility company’s point of view, than raising the average operating power factor of the network from 0.7 to 0.9 means:

- Cutting costs due to ohmic losses in the network by 40%
- Increasing the potential of production and distribution plants by 30%.

These figures speak for themselves: it means saving hundreds of thousands of tons of fuel and making several power plants and hundreds of transformer rooms available.

Thus in the case of low power factors utility companies charge higher rates in order to cover the additional costs they must incur due to the inefficiency of the system that taps energy. It is a well-known fact that electricity users relying on alternating current – with the exception of heating elements – absorb from the network not only the active energy they convert into mechanical work, light, heat, etc. but also an inductive reactive energy whose main function is to activate the magnetic fields necessary for the functioning of electric machines.

Power Factor is also defined as cos Ø = kW / KVA

Since **kVA = kW + kVAR** decreased **kVAR** requirement from the system has will result in decreased **kVA** requirement, which will consequently result in lower current consumption from the source.

Point to be noted in this case that any load which was operating at a power factor of **0.85** before compensation continues to operate on same power factor of 0.85 even after compensation. It is the source power factor which has been improved by compensating the kVAR requirement of that particular load (or group of loads) from parallel connected capacitor banks. The source is now relieved of providing some amount of kVAR (**=kVAR1 – kVAR2**).

COMPENSATED kVAR =

kVAR1 – kVAR2 = kW tanØ1 – tan Ø2 = kW [tanØ1 – tan Ø2]

Hence Required Rating of Capacitor banks to be connected = kW [tanØ1 – tan Ø2]

**Where,**

**cos Ø1** = Operating Power Factor

**cos Ø2** = Target Power Factor or Power Factor after improvement.

^{nd}part –

**Capacitor Banks In Power System (part two)**

4 example calculations of compensation for reactive power | EEP

[…] at 400 V and the power factor is to be compensated from cosφ = 0.75 to cosφ = 0.95. Determine the required capacitive power. The power and current before compensation […]

joseph Mankesi

I have a Problem : we have bought new PF Controller after the previous one malfunctioned. Now what is happening is that, the value of PF before controller goes on one step is 0.82, if the controller starts first step PF starts decreasing instead of increasing, such after fourth step the PF is 0.7. I have tried to see the settings of the controller are ok. The current of the capacitor is 35A each phase.

Engineers can you help me what to please.

Harun rashid

How to derate 110KV EHT level capacitor bank:

we had 30MVar cap. bank

each cell has 416.67 KVar, Cn=9.48micofarad,In=35.22A, Un=11.83KV

Cap.bank trips on unbalanced current relay.

uttam ponkiya

I get really good knowledge thanks bro.

In HVDC line how power factor affects?

Which type of power factor correction to use | EEP

[…] This is the method reaching a compromise between the inexpensive solution and the proper management of the installation since the benefits deriving from power factor correction shall be felt only by the line upstream the point where the capacitor bank is located. […]

How can I select the right capacitors for my specific application needs? | EEP

[…] deciding which type of capacitor installation best meets your needs, you’ll have to weigh the advantages and disadvantages of each and […]

Fahad

just to adjust the mistake

kVA^2 = kW^2+kVAR^2

it mean that

kVA = sqrt( kW^2+kVAR^2 )

not

kVA = kW+kVAR

and thank you for this useful articale

zaimi

Gd knowledge..

Rajiv G Desai

Love to get the news latter

Sabin Brunet

If a load was operating at .85 PF before correction, does it mean that, say a motor operating at .2 pf before correction will be raised by the capacitor bank? Or will it be simply the source PF that will be raised?

JIMBO_2013

Thanks for sharing the knowledge. Would you have information on how to interpret breaker schematics for SEL relays and breakers used in HV and EHV substations?

Thanks!

What's so important in role of capacitors in distribution systems? | EEP

[…] Flickr)Power factorShould the voltage on a circuit fall below a specified level for some reason, a device called a capacitor can momentarily maintain the voltage at line value. Basically, a capacitor serves the same purpose […]

mohammad alqasem

Thank you

nidhin47

Thank you for the simple explanation

Shielding Of Power Cables | EEP

[…] in corona discharge, and eventual destruction of the insulation.As well, leakage current and capacitive current through the insulation presents a danger of electrical shock. The grounded shield equalizes […]

Reducing Distribution Line Losses | EEP

[…] requirement, we only need one bank. If the size is 1/6 of the feeder requirement, we need five capacitor banks.2. Locate the first bank Start from the end of the circuit. Locate the first bank at the point on […]

What's common for Beer Mug and Power Factor? | EEP

[…] Excel Spreadsheet)Size of Capacitor For Power Factor ImprovementsHow Power Factor Corection WorksCapacitor Banks In Power SystemEconomic advantages of power factor correctionResource: powerstudies.com google_ad_client = […]

How to Protect Capacitor Banks? | EEP

[…] How to Protect Capacitor Banks? Introduction Capacitor banks are used to compensate for reactive energy absorbed by electrical system loads, and sometimes to […]

Shunt Reactor Used In HV and EHV Systems | EEP

[…] it is preferred to have reactive load support from other sources of reactive power like fixed Capacitor banks or other FACTS .Shunt Reactors are Inductive device commonly used in HV and EHV Systems for […]

Fundamental concepts of insulation testing | EEP

[…] of voltage affects insulation. Insulation Current Flow (AC)Insulation may be simply modeled as a capacitor in parallel with a resistor as shown in Figure 1. The current flow that results will comprise two […]

Short review of resistance, reactance and impedance | EEP

[…] are developed in proportion to applied voltage or current. respectively; but most notably in capacitors and inductors. When alternating current goes through a pure reactance, a voltage drop is produced […]

Capacitor Banks In Power System (part two) | EEP

[…] that always would be optimal correction. (pic by energolukss.lv) Continued from part one – Capacitor Banks In Power System (part one)Sizing of switching device for Capacitor banksIt should be noted that in an inductance the current […]