IEC 60439, the standard for low-voltage switchgear and controlgear assemblies, was under restructuring from the last decade. The new series of IEC 61439 standards were published in January 2009. This standard has brought considerable clarity in technical interpretation.
The new standard follows the philosophy of IEC 60947 series i.e. IEC 61439-1 is ‘General Rules’ standard to be referred to by subsidiary product parts of IEC 61439 series.
The IEC 60439 standards were ambiguous about how to assess compliance of partially type tested assemblies. As a result manufacturers and testing bodies often treated partially type-tested assemblies differently.
The three different but equivalent types of verification methods are introduced and these are:
- Verification by Testing
- Verification by Calculation/Measurement
- Verification by Design rules
The requirements regarding short circuit performance, temperature rise, dielectric properties and rated diversity factor have been covered in more detail.
|Title:||Introduction to IEC 61439 – A new standard on Switchgear and Controlgear Assemblies|
|Download:||Right here | Get Download Updates | Get Technical articles|
Recommended EE articles //
Page edited by E.C. (Google).