# Cable Designing Program (Spreadsheet)

Home / Download Center / Electrical Software / Cable Designing Program (Spreadsheet)

## Calculation of voltage drop and cable size

### Motor / Electrical load

• Calculate Voltage drop of Cable.
• Calculate  Size of Cable.
• Calculate Current Capacity of Cable.
 Software: Cable designing program Version: 22.8.2012 Developer: Jignesh Parmar Size: 99 Kb Price: Free Download: Right here | Get Download Updates | Get Technical articles

### Premium Membership

Premium membership gives you an access to specialized technical articles and extra premium content (electrical guides and software).

Page edited by E.C. (Google).

### 43 Comments

1. haitham
Dec 28, 2017

THANK U SO MUCH

2. michael eaton
Mar 16, 2017

Some people criticizing the calculations. There are many packages on the market that will calculate your cable size, volt drop etc. but at the end of the day you need to know what your doing. Even the best packages will throw up errors in calculations and if using these packages, you need to be knowledgeable to validate the output.
This is a good tool to get you to the result you need, but you need to know what your looking at, not blame someone else for producing a tool that dumbs down what you should be competent in knowing.

3. Ganesh
Oct 30, 2015

very useful spread sheets.thanks

4. hquocphu
Oct 14, 2015

SOMETHING WRONG IN DATASHEET:

PLPE resi
4cX4 5,53
4cX 6 3,7
4cX 10 2,29
4cX16 2,45
4cX 25 1,54
4cX35 1,11
4cX 50 0,082
4cX70 0,57
4cX 95 0,41
4cX 120 0,33
4cX 150 0,27
4cX 185 0,21
4cX 240 0,16
4cX 300 0,13
4cX 400 0,1
4cX 500 0,1
4cX 630 0,1

AND PVC

4cX4 8,89
4cX 6 5,53
4cX 10 3,7
4cX16 2,29
4cX 25 1,44
4cX35 1,04
4cX 50 0,77
4cX70 0,53
4cX 95 0,38
4cX 120 0,3
4cX 150 0,25
4cX 185 0,2
4cX 240 0,15
4cX 300 0,12
4cX 400 0,09
4cX 500 0,09
4cX 630 0,09

5. cahyo widodo
Oct 13, 2015

Please review bout voltage in your spreed sheet Mr. Jigness Parmar for the data in value cable if we implement type of cable Lt PVC arround of range cable size 4cX70 and 4cX95, the value of voltage drop so annoying me. The value of Voltage drop if we use 4cX95 should be smaller than we use 4cX70, but there is become bigger. i have put the value but i found the miss calculation i think, pardon me. Please review and give the your best development sir.

6. N M Venugopal
May 29, 2015

how do we size the cable when we have only load say 55 kW for a distribution board(3 pumps and lighting load) and at 415 v supply and a length of 400 m from source voltage to board.

7. M G Patel
Nov 08, 2014

Useful information

8. Parag Chamuah
Oct 13, 2014

Thanks for the work you have shared. I have few queries:
1.How do we know what is the phase value(φ)?
2.What is demand factor specifically?

9. bdthang
Jun 17, 2014

Very useful. It help me a lot!

10. kolumb
Jun 10, 2014

There is something wrong with the cable data – it’s impossible 3 different type cables with same Conductor Area, same matherial, to have 3 different Resistance (ohm/km).
Example – look first 3 cable types – PVC flexible, PVC insulated and XLPE insulated, for the same Conductor area (by example 1cX6), both Copper, resistance for the fist is 3.3ohm/km, for the second is 3,69ohm/km and the third is 1.53ohm/km.
May be the last one uses a super copper, twice better than first 2 :)

11. ENGR.MUHAMMAD YOUNAS KHAN
Apr 21, 2014

dear sir
I want to submit the formulas of cable sizing to those persons which are searching here and there.I appreciate of your current website which are publishing my cable sizing ideas.I am submiting another voltage drop and cable sizing formula.

1- Vd = 1.732 x I X L X PF/ (Area mm2 x conductivity of copper) ———-FORMULA 1
2- Area(mm2) = 1.732 x I X LX PF/(Vd x conductivity of copper) ———–FORMULA 2

WHERE:-
1.732 FOR THREE PHASE.
2 FOR SINGLE PHASE.
I = LOAD CURRENT.
L= LENGTH OF CABLE.
PF= POWER FACTOR.
Vd= VOLTAGE DROP.
CONDUCTIVITY OF COPPER AT 90 DEG.C = 41.66
CONDUCTIVITY OF ALUMINUM AT 90 DEG.C =25.64

DATA:-
1.732 FOR THREE PHASE.
I = 160 AMPS.
L= 200 METERS.
PF= 0.85

FIRSTLY WE CALCULATE THE VOLTAGE DROP.
Vd = 1.732 x 160 x 200 x 0.85/(70 mm2 x 41.66)
= 16.1547 volts —————(1) for copper conductor.
Area(mm2)b= 1.732 x 160 x 200 x 0.85/(16.1547 x 41.66)
= 70 mm2 ———-(2) for copper conductor.

if you want to use Aluminum conductor, apply conductivity of Akuminum which is above said.ABOVE CALCULATIONS ONLY FOR THREE PHASE.

FROM
ENGR.MUHAMMAD YOUNAS KHAN
M.SC.ENGG.MIEE(UK)
WAZIRABAD CITY, PUNJAB,PAKISTAN.

• Ramkumar M
Mar 07, 2015

How you get Area size 70mm2 ?

• jan
Apr 30, 2015

i dont have a voltage drop and sq.mm.i have only amps how did we calc the sqmm

• Ch. Khalid Parvez Akhtar
Jul 28, 2015

Its a wonderful working.I must compliment you for this great work. Congratulations
Regards
Ch. Khalid Parvez Akhtar
Jalalpur Jattan
Gujrat
Pakistan

12. thiru
Apr 19, 2014

calc is wrong.Diff cable size should apear for Al & Cu.

• m daley
Nov 20, 2015

can you give me the formula for calculating cable sizes please

13. osman
Jan 04, 2014

please send me

14. Kingsley
Jan 01, 2014

Very useful, Thanks.

15. thanasusankar.bec@gmail.com
Nov 14, 2013

Sir,
I have a query in cable designing excel spread sheet Ver.22.8.12, I would be much thankful If would get it clarified.
In sizing of cable for motor feeder, The “KW” entry is mentioned what? It is the mechanical output or electrical input. If it is the mechanical output, the actual electrical load consumed must be output/efficiency and the actual input current is
Full load ampere = Output power/(1.732*P.F*V*Eff)
If “KW” Entry is actual input power then Full load ampere = Input power/ (1.732*P.F*V), Efficiency is not required in this case.
But, in your case, the “KW” entry is multiplied with efficiency to obtain actual load consumed (May be the mechanical power output which is less than “KW” entry) and the motor amperage is calculated from the actual load consumed. In such a case loses may not be able to feed to obtain desired full load output.

As far as demand factor concerned it (Load factor) is okay.Please clarify.
T.Sankar

16. Accesstel
Sep 22, 2013

Hi guys please let me know if we can buy these tools if they are not downloadable. I have invested 4 hours now with no success.

17. Rajesh SV
Sep 07, 2013

Hi EEP members…..Am not able to download any of the spreadsheets…Plz advice.

18. Jonesy
Aug 09, 2013

cannot down load!

19. Arnon
Jul 27, 2013

Nice !!!!!!

20. Donie
Jul 23, 2013

Useful! :)

21. wnirut
Jul 02, 2013

thank you

22. engele
Jun 18, 2013

Hi there,

would appreciate it if you could send a copy of the excel file to emile.engel@petrosa.co.za thanks

23. gabrielovskys
Jun 17, 2013

Tried but still i am not able to download the spreadsheet after login. Please kindly send excel file to gabriel.garcia@iie.org.mx……. Thank you

24. celebrationcometh
Jun 17, 2013

Tried but still i am not able to download the spreadsheet after login. Please kindly send excel file to ooluwakueshe@yahoo.com. Thank you

25. celebrationcometh
Jun 17, 2013

Same here. not able to download the spreadsheet too after log in.
Please help out

26. gurunadh006007
Jun 05, 2013

hello
i want to know the logics so please provide me password for this cable designsheet

27. sam atlantis
May 28, 2013

The link is not working even after LOGIN. Pls update the link.

• Edvard
May 28, 2013

Hi,

Make sure to enable cookies in your browser. If cookes aren’t enabled, browser doesn’t know when you’re logged in.

I just checked, this spreadsheet has been downloaded 4763 time so far ;)

Hope you will make it!

28. neeraj tiwari
Apr 25, 2013

i am unable to download excel sheet suggest me for same.

29. neeraj tiwari
Apr 25, 2013

i m not able to download excel sheet suggest me for same.

30. GnMvP
Dec 23, 2012

No DC cables?

31. Hamada666666
Mar 30, 2012

very good program

32. Veeraraghavan VS
Jan 07, 2012

Dear Edvard,

I tried the cable selection excel sheet. It is very good. I am giving below my observations.

1. Why there are 2 PFs? C9 and C10 are OK. Why C15?
2. Once a 3 Ph motor is selected, all single core and 3.5core cables may disappear from the list for selection.
3. In the results, Starting voltage drop as % will be helpful to refer.
4. It may be better if the TDF (Total Derating Factor) considered in selection is displayed.
5. As a case study, i considered a 55KV, 433V, 3Ph motor. DOL Start, 0.85 Running PF, 0.3 Starting PF, 85% efficiency, 600m length, LT XLPE Al cable, 3 trays, 6 cable per tray, cables touching each other. According to my earlier calculation 3cx50 cable is not suitable – 10.23% Running voltage drop and 24.41% starting voltage drop. But this sheet is showing OK with 1.95% running voltage drop.

The TDF considered by me is 0.674. Of course, the resistance and reactance data are from Indian cable manufacturers.
Please let me know your opinion / observation. 3cx50 al cable for a 55KW motor in DOL starting for 600m distance – please check.

33. Pedro Abarca
Oct 12, 2011

My coment is that I need a electrical software

• jm010809
Oct 16, 2012

I use manual calculations since not all form of installation is covered on this spread sheet….

#### Premium Membership

Get access to premium electrical guides, technical articles and much more!