## Input fields As per ANSI/IEEE Std 80-1986 code

- Length of Area Occupied by Earthing Grid
- Width of Area Occupied by Earthing Grid
- Fault level at Incoming Bus
- Incoming Voltage
- Outgoing Voltage
- Soil Resistivity
- Resistance of Main Earthing Mat
- Resistance of surface Material (Crushed Rock )
- Thickness of Surface Material (Crushed Rock)
- Depth of Earthing Grid Conductor
- Diameter of Earthing Grid Conductor
- Reference Depth of Grid
- Spacing between Parallel Conductor of Grid

## What this Spreadsheed does?

- Program is design as per ANSI/IEEE 80-1986 Code
- Calculate Step Potential of Switch yard
- Calculate Touch Potential of Switch yard
- Calculate Total Length of Earthing Mat Conductor
- Calculate Size of Earthing Mat Conductor
- Calculate Total No of Earthing Rods

Software: | Earthing Mat Design For Substation |

Version: | 22.12.2012 |

Developer: | Jignesh Parmar |

Size: | 46 Kb |

Price: | Free |

Download: | Right here | Get Download Updates | Get Technical articles |

NIDHI

Sir,

In the design procedure for earthing it is said that as we doubles the length of the rod the resistance will be reduced by 40% and when we increase the size of the electrode the resistance decreases by 10%. i am getting this . with reference to what equation the above mentioned conclusions is reached

Murugesan.C

I am not able to see the detailed drawing about construction of earth mat. A drawing shall be presented indicating driving/penetrating number of MS rod in ground and connecting all of them by a earthing flat/strip. Illustration of such drawing may help the young engineers to learn and execute.

Nadun

Could u please explain me how to do the earth mat design for 220/132/33 kV Outdoor GSS which have 5 steps (135m, 138m, 141m, 144m, 147m).

Can’t do the Earth mat design separately for each step and finally connect each steps together. OR is it must to do the design for all the steps together?

Since their is huge civil work in step 144m and 147m it may take some time, so we can start lower 3 level works if we can lay the earth mat.

Thank you!

RAJEEV SINGH

I want to design the Earthmat of Solar Park of 10MW consisting of 10 Nos. step up transformers spreading over huge land area, which is evacuating the power at 11kV level. Please suggest:

i) whether the each earth mat is to be connected.

ii) for DC earthing separate mat is provided?

iii) spacing between conductors and material??

radixit

I want to design the earth mat of a 33/11 kv substationat kanpur for which i want to know the fault current the resistivity we have found 22 ohm met and IEEE80 formule is not available,there fore I WANT YOUR HELP

ramesh

Among the inputs data, i don’t understand what you mean by the following, which is both required in your program:

i) Reference Depth of Grid and Depth of Earthing Grid Conductor

ii) Diameter of Earthing Grid Conductor or size of earthmat flat

iii) Number of adjacent earthing mat conductors

iv) How evaluate the values Ks, Df

Kindly explain what you mean by these terminologies, and where to get such inputs.

Robinson

Among the inputs data, i don’t understand what you mean by the following, which is both required in your program:

(i) Number of adjacent earthing mat conductors

(ii) Margin factor in earthing mat against corrosion and rusting.

Kindly explain what you mean by these terminologies, and where to get such inputs.

esaivani

sir,

explain the brief note for earth mat calculation

Eric.Bernays

Is there a version for use in the UK?

mcalderac

thanks for this page. ***** five stars !!!!

dieng

Great Job man! Thanks a lot!

Roshan Mathew Verghese

Hi edvard,

could you put up an article for measuring the Earth Resistance, Step & Touch potentials, using a Injection transformer ?

akira

Dear Sir

Thank you for this subject , i need to know how to determine required no. of earthing rods?

Regards

RAGHAVENDRA KUMAR

Can u send me the details required to design an earth mat for 132/33KV Substation which the area consist of 12400 Sqm and 13620 SqM?

keLvinz0r

GREAAAAT JOB!

I’M YOUR FAN!

Pandiyan

Sir,

Can u send me the details required to design an earth mat for 230/110KV GIS Substation which the area consist of 60by 75 mtrs?