## 1. Introduction

A suspension insulator strain consists of a series of * alternately insulators* and

*, which bind each insulator to the next. This constitutes a*

**metal parts***, with each one’s capacitance being created by two successive metal connectors (*

**series of connected capacitors***clips*) with the porcelain as a dielectric.

*between each connector and the support arm or the tower.*

**air capacitances**So let us consider a strain of four suspension insulators, as shown in the figure below, and let C be the same capacitance for each unit and kC the capacitance of each metal connector with earth.

Then, if * V_{1}* is the potential difference between the two metal connectors (

*clips*) of the first insulator, we have:

Even * V1 + V2 + V3 + V4 = E* (phase voltage of the line) →

**E = V1 (4 + 10k + 6k**^{2}+ k^{3})**So, if k = 0,1, we have:**

### 2. Corona rings

The distribution of the potential along the insulators strain can be improved by using a * smoothing ring (Corona ring)* or a

*, which consists of a large metal ring surrounding the last insulator that is electricallyconnected to the line.*

**protective ring**The corona ring inserts capacitances between the metal connectors (*clips*) of the insulators and the line. For these capacitances, special care can be taken in order to compensate the capacitances to earth.

### 3. Cases of insulators strains with or without Corona rings

#### Case 1

Determine the * potential distribution* in a strain of three insulators, if the capacitances of the links to earth and to the line are respectively

*and*

**20%***of the capacitance of the insulators. Also, determine the performance of the strain.*

**10%**#### Case 2

An overhead 3-phase transmission line, which has phase voltage * 30 kV*, is hanging from a

*. The capacitance between the links and the earth is*

**three insulators suspension strain***, where C is the capacitance of an insulator.*

**0,2 C**- Determine the potential distribution along the insulators strain.
- If a
inserts capacitances from the line, with the link of the middle and the lower insulator set at**protective (corona) ring**and the link of the medium and the higher insulator set at**0,4 C**, find the new distribution.**0,1 C**

##### 2.1 Determine the potential distribution along the insulators strain

##### 2.2 Protective (corona) ring inserts capacitances from the line

### 4. Generalized formula of voltage distribution in a suspension insulators strain

The above mathematical formula is the generalized formula we can use to find the voltage Vn of the (n-1) insulator.

E = phase voltage of the line.

The value of ‘a’ is given by the above formula:

#### 4.1 Determine the voltage distribution in a six insulators strain (z=6) with k=0,1

#### 4.2 Determine the voltage distribution of the first, the sixth and the twelfth insulator with z = 12 (12 – insulators strain) and k = 0,1

We have:

###### References:

– Generation, Transmission, Distribution, Measurement and saving of Electrical Energy**Vasilios N. Xanthos**

General principles of electricity supply systems | EEP

[…] Figure 1 shows a suspension tower on the National Grid network. […]

B Ram

please convey me the C value of :

What is the capacitance value of 11 kv disk insulator?

What is the capacitance value of single long rod insulators used at 145 kv and 245 kv line to line voltage?

r. collantes

nice explanation >>>

15 hypothesis responsible for the aging of composite insulators | EEP

[…] be accelerated and insulator failure may occur after a few years of exposure. Surveys indicate that some insulators operate well for 18–20 years and others fail after a few months.An analysis of laboratory data and literature surveys permit the […]