Save 50% on all EEP Academy courses with Enterprise Membership Plan and study specialized LV/MV/HV technical articles & guides.

# Calculating lightning strike distance

Home / Technical Articles / Calculating lightning strike distance

## Lightning strike distance

Return stroke current magnitude and strike distance (length of the last stepped leader) are interrelated. A number of equations have been proposed for determining the striking distance.

The principal ones are as follows:

1. S = 2 x I + 30(1−e − I / 6.8) –  Darveniza (1975)
2. S = 10 x I0.65Love (1987; 1993)
3. S = 9.4 x I2/3Whitehead (1974)
4. S = 8 x I0.65IEEE (1985)
5. S = 3.3 x I0.78Suzuki (1981)

where:

S is the strike distance in meters
I is the return stroke current in kiloamperes

It may be disconcerting to note that the above equations vary by as much as a factor of 2:1. However, lightning investigators now tend to favor the shorter strike distances given by Equation 4.

Anderson, for example, who adopted Equation 2 in the 1975 edition of the Transmission Line Reference Book (1987), now feels that Equation 4 is more accurate.

Mousa (1988) also supports this form of the equation. The equation may also be stated as follows:

I = 0.041 x S1.54

SOURCE: Robert S. Nowell, Georgia Power Company

Get access to premium HV/MV/LV technical articles, electrical engineering guides, research studies and much more! It helps you to shape up your technical skills in your everyday life as an electrical engineer.

### Edvard Csanyi

Electrical engineer, programmer and founder of EEP. Highly specialized for design of LV/MV switchgears and LV high power busbar trunking (<6300A) in power substations, commercial buildings and industry facilities. Professional in AutoCAD programming.