CYBER WEEK OFFER 💥 Save 20% on PRO Membership Plan and Video Courses with the coupon CYM23 (Expires in 2 days).

# How to make calculation for a distribution substation 10/0.4 kV, 2×1600 kVA

Home / Technical Articles / How to make calculation for a distribution substation 10/0.4 kV, 2×1600 kVA

## Introduction to calculations

Distribution substations with an installed power of 2×1600 kVA are a typical example of electrical power supply facilities which can be often seen all around Europe and wider. By “calculation” of such a substation, it is assumed that values of all relevant physical quantities shall be determined, and all major equipment inside the substation shall be specified according to these values.

Within this article, an example of this type of calculation for electrical equipment will be given.

A basic guide for calculations and dimensioning will be adequate IEC standards and practical engineering experience. Of course, besides electrical, there will be also civil and HVAC (Heating Ventilation and Air Conditioning) requirements for substation which need to be fulfilled, but they are out of the scope of this article.

Contents:

## 1. Substation example

When we say “2×1600 kVA” that means two power transformers, each of them with rated power of 1600 kVA, will be installed inside substation.

Strictly speaking, but not necessary, 2×1600 kVA designation assumes a substation capable to cover a peak power demand of 2×1600=3200 kVA. That further implies a parallel operation of transformers, i.e. both transformers will carry the load at the same time.

On the other hand, when we want to emphasize that one transformer will be a working unit, while the other serves as a spare, a designation (1600+1600) kVA may be used. The latter means that the substation will be designed for a peak power demand of 1600 kVA.

As explained above, the operation mode of two transformers, i.e. designed peak power of substation is the first important requirement which needs to be defined prior to further design.

This example will be based on 3200 kVA peak power demand requirement. Besides that, other major input data necessary for calculation and design are:

• Medium voltage rated value
• Low voltage rated value
• Medium voltage network short circuit power (or short circuit current)
• Number of medium voltage power supply cables
• Type of earthing arrangement
• Maximum ambient temperature

Single line diagram of distribution substation is given in Figure 1. Substation is supplied from 10 kV distribution network via two cables (typical solution for so called ring type of supply).

Medium voltage switchgear (design tag +K) supplies power transformers (design tag -T1 and -T2) with voltage transformation ratio of 10/0.4 kV/kV. Power is further distributed to consumers on 0.4 kV voltage level via busbar system (design tag BT1 and BT2) and main low voltage distribution switchboard (design tag +1NE).

The number and rating of outgoings, i.e. circuit breakers, inside +1NE switchboard is determined by predicted or actual number and consumption of consumers supplied from this substation.

This technical article/guide requires a Premium Membership. You can choose an annually based Plus, Pro, or Enterprise membership plan. Subscribe and enjoy studying specialized technical articles, online video courses, electrical engineering guides, and papers. With EEP’s premium membership, you get additional essence that enhances your knowledge and experience in low- medium- and high-voltage engineering fields.

Check out each plan’s benefits and choose the membership plan that works best for you or your organization.

CYBER WEEK DEAL 💥 – Save 20% on PRO plan with the coupon CYM23.