Black Friday DealðŸ’¥

Save 20% with a coupon BLCK20 on PRO Membership Plan and all courses at the EEP Academy! Learn from experienced engineers!

# How capacitors improve the power factor and how to calculate them?

Home / Technical Articles / How capacitors improve the power factor and how to calculate them?

## How to improve the power factor?

It’s quite simple. By installing capacitors or capacitor banks. Improving the power factor of an electrical installation consists of giving it the means to “produce” a certain proportion of the reactive energy it consumes itself.

There are various different systems for producing reactive energy, including in particular asynchronous compensators and shunt capacitors (or serial capacitors for large transmission systems).

The capacitor is most frequently used, given:

1. Its non-consumption of active energy
2. Its purchase cost
3. Its ease of use
4. Its service life (approximately 10 years)
5. Its low maintenance (static device)

### Power diagram

Power factor is the ratio of working power to apparent power. It measures how effectively electrical power is being used.

Low power factor means youâ€™re not fully utilizing the electrical power youâ€™re paying for. A high power factor signals efficient utilization of electrical power, while a low power factor indicates poor utilization of electrical power.

To determine power factor (PF), divide working power (kW) by apparent power (kVA). In a linear or sinusoidal system, the result is also referred to as the cosine Î¸.

PF = kW / kVA = cosine Î¸ kVA

For example, if you had a boring mill that was operating at 100 kW and the apparent power consumed was 125 kVA, you would divide 100 by 125 and come up with a power factor of 0.80.

(kW) 100 / (kVA) 125 = (PF ) 0.80

Where:

• PÂ – Active power
• S1 and S2Â – apparent powers
(before and after compensation)
• QcÂ – capacitor reactive power
• Q1Â – reactive power without capacitor Q2: reactive power with capacitor

Equations:

• Q2 = Q1 – Qc
• Qc = Q1 – Q2
• Qc = PÃ—tg Ï†1 – PÃ—tgÏ†2
• Qc = PÃ—(tg Ï†1 – tg Ï†2)

Where Ï†1 is phase shift without capacitor andÂ Ï†2 is phase shift with capacitor

The capacitor is a receiver composed of two conductive parts (electrodes) separated by an insulator.Â When this receiver is subjected to a sinusoidal voltage, the current and therefore its power (capacitive reactive) is leading the voltage by 90Â°.

Conversely, for all other receivers (motors, transformers, etc.) the current and therefore its power (reactive inductive) is lagging the voltage by 90Â°.

The vectorial composition of these currents or reactive powers (inductive and capacitive) gives a resulting current or power below the value which existed before the capacitors were installed.

In simple terms, it is said that inductive receivers (motors, transformers, etc.) consume reactive energy whereas capacitors (capacitive receivers) produce reactive energy.

### How to calculate the power of capacitors

Based on electricity bills to calculate the capacitor banks to be installed, use the following method:

• Select the month in which the bill is highest (kVArh to be billed)
• Assess the number of hours the installation operates each month
• Calculate the capacitor power Qc to be installed
Qc = kVArh to be billed (monthly) / No. of hours’ operation (monthly)

Example for the subscriber //

• Highest reactive energy bill: December Number of kVArh to be billed: 70,000
• Monthly operating times: High-load + peak times = 350 hours

Qc (bank to be installed) = 70,000 / 350 = 200 kVAr

#### Based on measurements taken on the HV/LV transformer secondary: PkW-cosFI

##### Example //

An establishment supplied from an 800 KVA HV/LV subscriber station wanting to change the power factor of its installation to:

• CosÏ† = 0.928 (tgÏ† = 0.4) at the primary
• I.e. CosÏ† = 0.955 (tgÏ† = 0.31) at the secondary, with the following readings:
• Voltage: 400 V 3-phase 50 HZ
• PkW = 475
• Cos (secondary) = 0.75 (i.e. tg Ã¸ = 0.88)

Qc (bank to be installed) =Â PkW x (tgÏ† measured – tgÏ† to be obtained)
Qc = 475 x (0.88 – 0.31) = 270 kVAr

#### Calculation for future installations:

##### Example

1000 kva transformer, Q capacitor = 250 kVAr

Note: This type of ratio corresponds to the following operating conditions:

• 1000 kVA transformer
• Actual transformer load = 75%
• CosÏ† of the load = 0.80 } k = 0.421
• CosÏ† to be obtained = 0.95 } – see table below

Qc = 1000 x 75% x 0.80 x 0.421 = 250 kVAr

### Capacitor power calculation table

#### Conversion table

Based on the power of a receiver in kW, this table can be used to calculate the power of the capacitors to change from an initial power factor to a required power factor. It also gives the equivalence between cos Ã¸ and tg Ã¸.

Example: 200 kW motor – cosÏ† = 0.75 – required cosÏ† = 0.93 – Qc = 200 x 0.487 = 98 kVAr

Reference // Reactive energy compensation and power quality monitoring by Legrand

Get access to premium HV/MV/LV technical articles, electrical engineering guides, research studies and much more! It helps you to shape up your technical skills in your everyday life as an electrical engineer.

### Edvard Csanyi

Electrical engineer, programmer and founder of EEP. Highly specialized for design of LV/MV switchgears and LV high power busbar trunking (<6300A) in power substations, commercial buildings and industry facilities. Professional in AutoCAD programming.

1. Sirelkhatim Nugud
May 18, 2022

A very useful article
Thanks
Eng sirelkhatim

2. velmurugan ramakrishnan
Oct 12, 2021

very good

3. Deepak Agrawal
Aug 30, 2020

nice

### Subscribe to Weekly Newsletter

Subscribe to our Weekly Digest newsletter and receive free updates on new technical articles, video courses and guides (PDF).