Premium Membership ♕
Save 50% on all Video Courses with Enterprise Membership Plan and study specialized LV/MV/HV technical articles and guides.
By Edvard Csanyi | Sep, 5th 2018 | 9 comments | Translate | Save to PDF
Subscribe | Share!
Home / Technical Articles / Applying CTs in protection schemes for transformers, generators, machines etc.
Learn How to Design Power SystemsLearn to design LV/MV/HV power systems through professional video courses. Lifetime access. Enjoy learning!
Subscribe to Weekly NewsletterSubscribe to our Weekly Digest newsletter and receive free updates on new technical articles, video courses and guides (PDF).
The content is copyrighted to EEP and may not be reproduced on other websites.
Your method/type 5 may not work properly if the sheath material is ferro magnetic, the balance core CT has short circuit of magnetic flux at the possition installed.
My question is that i want to achieve Differential Protection of motor and i have following condition
Breaker side CT is 500/1 Amp
Motor Side CT is 200/1 Amp
is it possible or there will be some issue than what kind of issue.
I need weekly updates
the nomenclature or the element of doing the job is not clear as the theory is given but it is now some how clear for me thank you
This article is very important for me because concerning the theoritical analysis is ok but the instrument or the nomenclature of the element sensitive can say not very clear or situated
Nice Information Mr. Edwards
As always, this article by Mr. Edward is very informative. Thank you.
Cheers …. beautiful explanations.
I have a query and can it be raised here?
Very informative Article Edvard. Cheers