SHP plants up to 25 MW
This standard/manual guideline covers selection of systems for control, automation, protection and monitoring for small hydropower plants (SHP) up to 25 MW by developers, manufacturers, consultants, regulators and others. This includes selection of technology, extent of automation and monitoring system for different categories of SHP.
Up to 100 kW, up to 5 MW and 5 MW to 25 MW) which are economical, easy to adopt, sustainable, feasible and essential for safe operation.
The generating units of a SHP plant may have its shaft vertical, horizontal or inclined with the type of turbine selected to suit the site’s physical conditions. Small hydro turbines may be selected as per site conditions, head and discharge available.
Small hydro-generator are of the alternating current type and may be either synchronous or induction type.
Usually SHP units up to 5 MW are expected to require minimum of field assembly and installation work. While units having capacity from 5 MW to 25 MW may have slow speed, large diameter and with split generator, stator that may require final winding assembly in the field.
Provision of parallel operation with other systems will have more comprehensive control, monitoring & protection system. This guideline will serve as a reference document along with available national and international codes, standards, guide and books.
For the purpose of convenience this standard / manual guidelines has been subdivided as follows:
- Control and Automation
- Protection and Relaying
- Metering and Monitoring
|Title:||Selection of control, automation, protection and monitoring system of a small hydro power plant – Dr Arun Kumar|
|Download:||Here » Get EEP Membership | Video Courses | Download Updates|