Voltages ratings in data center electrical distribution
Voltage standards are usually stated using two values such as the IEC standard 400/230V or the North American voltage 415/240V for high-efficiency green data centers. However, IT professionals still have difficulty understanding what this means.
What is the relationship between these two values? What’s the difference between the IEC and North American voltage standard? Why is 100-240Vac input voltage shown on the label of the servers in our data center?
To better understand data center electrical distribution voltages, it is helpful to learn about the electrical distribution equipment itself.
Three-phase system vs. single-phase system
The electrical distribution in data centers is typically an alternating current (AC) three-phase system.
Transformers found in data centers are typically three-phase (three separate coils) and step down from a higher input voltage (also known as primary voltage) to a lower output voltage (also known as secondary voltage).
The terms “3-wire” and “4-wire” are often used to describe the electrical system design. The term 3-wire means that there are three “hot” conductors, line 1, 2, and 3 shown in Figure 1 above.
While the term 4-wire means that in addition to three “hot” conductors there is a fourth “neutral” conductor. The neutral is required to supply line-to-neutral voltage to most IT loads as shown in Figure 2.
This is accomplished by connecting a ground wire to all exposed metal parts of all equipment (including IT equipment) in the data center. In the event of a phase to ground fault, the ground wire acts as a low resistance path for current to flow which opens the circuit breaker or fuse.
In summary, there are two types of three-phase systems: 3-wire plus ground and 4-wire plus ground. In some regions, the 4-wire plus ground system is referred to as a 5-wire electrical system.
|Title:||The Basics Of Electrical Distribution Equipment In Data Centers (For IT Professionals) – Pearl Hu (Schneider Electric)|
|Download:||Right here | Get Download Updates | Get Technical articles|