Power cable sizing adjustment
The initial aim of the thesis is to provide new findings in term of power cable sizing adjustment which later is deemed right for normal operating purposes.
There are a few objectives that the thesis should meet upon completion:
A – To obtain a certain value of constant, K which can be use in determining appropriate size of power cable that is being subjected to harmonic influence. The constant also take issues of safety and reliability into consideration.
B – To investigate the correlation between THD content (harmonic in percentage) to the temperature properties of power cable. This is made possible by designing a specific experiment for this purpose.
C – To perform a method of selection of power cable size that is deemed safe and proportional to the ability to contain particular magnitude of current.
The problem with harmonic existence in power cables is that every component which frequency is dependent, namely current and voltage is easily manipulated.
As the frequency rises, magnitude of current also increases and the temperature heats up.
However, under harmonic influence, the loss is no longer the same as the sinusoidal current transmission loss as in the power cable, there is a combination of fundamental and harmonic current. The additional harmonic current certainly causes more loss and it is a concern of the thesis.
Thus, this thesis tends to concentrate on the determination of proper sizing of power cable, subject to the harmonic content. The correlation between THD and temperature properties of power cable is found by experiments performed during data collection process.
The project conducted thorough examination upon cable size(s) that seemed to be able to contain additional magnitude of current and the resulting loss (temperature) under harmonic influence.
Historically, power cable sizing, especially neutral line is based on the understanding of the harmonic current can be at most, 1.73 times the phase current (Gruzs, 1990). Meaning, the usual sizing would be the neutral cable to be twice the same of phase current, and eliminating every possibility that harmonic may cause the magnitude to be higher than two times phase current.
A certain calculation of ampacities and sizing of line and neutral cable in the presence of harmonics has open the path of determining the exact requirement in term of cable sizing toward certain amount of harmonic (Hiranandani, 1995).
Under normal working ampacity of cable, the loss is already predicted by the manufacturers. The information provides manufacturers valuable information to design their products and market them accordingly.
Thus, the loss supposedly increased to a certain magnitude. The resultant loss needed to be investigated so that the maximum permissible loss is not exceeded or else the operation of cable is under possible severe damage.
|Title:||Determining Correction Factor of Power Cable Sizing – Muhammad Mokhzaini Bin Azizan|
|Download:||Right here | Get Download Updates | Get More With Premium Membership|