Design calculations establish minimum guidelines and requirements for generating electrical calculations on projects. Electrical calculations should be made for all projects that include electrical components and should be filed in the project notebook.
Design calculations may be made either manually or by computer programs. At a minimum, the following types of calculations should be made where applicable:
- Load calculations
- Conductor sizing
- Conduit sizing
- Motor branch circuit sizing
- Power factor improvement
- Transformer primary and secondary circuit sizing
- Voltage drop
- Motor starting voltage dip
- Short circuit analysis
- Lighting levels
- Grounding in substations (where step potentials are of concern)
- Harmonic distortion analysis
- Cable pulling calculations
- Generator capability/motor starting.
Load calculations should be made using applicable sections of NEC Articles 220, 430, and other sections of the NEC.
The following load calculations should generally be used for sizing:
- Feeder conductors and protective devices
- Panelboard and switchboard main busses
- Motor control center components
- Service entrance devices and conductors
An allowance must be made for future load growth. The loads for each branch of the distribution system can then be summed back to the service entrance equipment.
The following information is intended to familiarize the design engineer with terms used by generator sizing software and underlying formulas.
Generator single or multi-sets must be sized to supply maximum starting (SkVA), stead-state running (RkVA) and non-linear (GkW) demands of connected and future electrical equipment.
Information critical to the sizing and selection of generator single or multi-sets include:
- Environmental conditions: elevation, temperature, indoor or outdoor
- Noise abatement requirements: mufflers, enclosure, silent models
- Fuel: diesel, gasoline, natural gas
- Fuel storage: skid mounted tank, day and remote tanks
- Cooling: liquid cooled radiator, forced air
- Voltage regulation: maximum allowable voltage dips
- Operation: prime, standby
- Voltage ratings: voltage, 3-phase, 1-phase, solid grounded, delta, wye
- Connected loads: Linear, non-linear, power factor
- Load operation: Motor starting methods, single step, single step with diversity, multiple steps of loading
- Future loads
Sizing Procedures for Generator Single or Multi-sets
The following is the sizing procedure for generator single or multi-sets:
- Prepare a load schedule.
- Enter individual load characteristics in software.
- Enter loads in step sequence in software.
- Have software calculate and select a generator set.
It is a good practice to request a verifying calculation from the preferred genset manufacturer.
|Title:||Electrical Design Calculations Needed For Projects – Seattle Public Utilities|
|Download:||Here 🔗 (Get Premium Membership) | Video Courses | Download Updates|
Can you send me the Electrical Design Calculation pdf.
Very nice article. Can you please send me the PDF of Electrical design calculation as well?
Thank you very much.
how I can get PDF?
how can get the electrical calculations laws .. i’m electrical superviosor
This article is very informative.
Please send me the PDF copy.
please send the pdf of this topic: Electrical Design Calculations Needed For Projects
Thank, Can you send me the PDF..
I am beginner in Electrical engineering and would like to grow in terms of design. Please assist
Thanks. This article is much useful.
Good Day dear Arokia
Would you please to send me this file, I am interested to get this file
Thank you in advance
Hello who may concern
Would you please to send me this pdf (electrical design calculations needed for projects)
I am interested to get this articular
Thank you in advance
I AM INTERESTED IN ELECTRICAL DESIGN CALCULATIONS , PLS KEEP ME UPDATED
thanks for the good job.
I’m interested in electrical design calculation on AC, and DC, and Solar system