Surge Protection Measures (SPM)
There are several surge protection techniques, which can be used to minimise the lightning threat to electronic systems. Like all security measures, they should wherever possible be viewed as cumulative and not as a list of alternatives.
BS EN 62305 defines this as a complete system of protection measures for internal systems against LEMP with the term Surge Protection Measures (SPM). BS EN 62305-4 describes a number of measures to minimise the severity of transient overvoltages caused by lightning and electrical switching.
Key and basic protection measures are:
- Earthing and bonding
- Electromagnetic shielding and line routing
- Coordinated Surge Protective Devices
Further additional protection measures include:
- Extensions to the structural LPS
- Equipment location
- Use of fibre optic cables (protection by isolation)
NOTES // For the purpose of this guide and its scope, protection measures utilising SPDs will only be considered. See BS EN 62305 for further details of all protection measures. Surge Protection Measures (SPM) were previously known as LEMP Protection Measures Systems (LPMS) in BS EN 62305
SPMs also have to operate within and withstand the environment in which they are located considering factors such as temperature, humidity, vibration, voltage and current.
Selection of the most suitable SPM is made using the risk assessment in accordance with BS EN 62305-2 taking into account both technical and economic factors. For example, it may not be practical or cost effective to implement electromagnetic shielding measures in an existing structure so the use of coordinated SPDs may be more suitable.
To ensure continuous operation of critical systems even in the event of a direct strike, SPDs are essential and these must be suitably deployed, based on the source of surge and its intensity using the Lightning Protection Zones (LPZ) concept within BS EN 62305-4.
|Title:||Selection, application and theory of surge protection devices (SPD) – BEAMA|
|Download:||Right here | Video Courses | Membership | Download Updates|
Which are the criteria to be considered when you go to market for buying a surge protecting device