What affects grounding resistance?
First, the NEC code requires a minimum ground electrode length of 2.5 meters (8.0 feet) to be in contact with soil. Soil composition, moisture content, and temperature all influence the soil resistivity, so it is recommended that the ground rods be placed as deep as possible into the earth to be most effective.
Nevertheless, four variables affect the ground resistance of a ground system:
1. Length/depth of the ground electrode
One very effective way of lowering ground resistance is to drive ground electrodes deeper. Soil is not consistent in its resistivity and can be highly unpredictable.
It is critical when installing the ground electrode that it is below the frost line. This is done so that the resistance to ground will not be greatly influenced by the freezing of the surrounding soil. Generally, by doubling the length of the ground electrode you can reduce the resistance level by an additional 40%.
There are occasions where it is physically impossible to drive ground rods deeper-areas that are composed of rock, granite, etc. In these instances, alternative methods including grounding cement are viable.
2. Diameter of the ground electrode
Increasing the diameter of the ground electrode has very little effect in lowering the resistance. For example, you could double the diameter of a ground electrode and your resistance would only decrease by 0%.
3. Number of ground electrodes
Another way to lower ground resistance is to use multiple ground electrodes. In this design, more than one electrode is driven into the ground and connected in parallel to lower the resistance. For additional electrodes to be effective, the spacing of additional rods needs to be at least equal to the depth of the driven rod.
Without proper spacing of the ground electrodes, their spheres of influence will intersect and the resistance will not be lowered.
4. Ground system design
Simple grounding systems consist of a single ground electrode driven into the ground.
The use of a single ground electrode is the most common form of grounding and can be found outside your home or place of business. Complex grounding systems consist of multiple ground rods, connected, mesh or grid networks, ground plates, and ground loops.
Complex networks dramatically increase the amount of contact with the surrounding earth and lower ground resistances.
|Title:||Measuring Earth Resistance – E. Hering, Dresden (Germany)|
|Download:||Right here | Video Courses | Membership | Download Updates|
Sir good morning my comment is regarding the residential power source supply Building.(PSSB) coming from Saudi electric company. WHY THE EARHTING AND NEUTRAL ARE IN ONE LOOP OR PARARELL CONNECTION. IF NOT AFFECTED THE TRANSFORMER IT SELF? AND ALSO THE LOAD SIDE OF THE BUILDING NOT AFFECTED DUE TO POWER FAILURE SOURCE SUPPLY?
Thank you very much
Sir, Your articles are amazing. I really appreciate your effort to bless and develop young Engineers.
Thanks in millions
differnce between earthing and grounding
Plz advice if my reading showing me 0.28. Is this good reading or good resistance. Thank you
If you get this value in ohms then it is okay, 3 to 10 ohms at interval of 20 meters distance is just good.
Very informative. Thanks alot
For subscription. Electrical engineer, working in defence manufacturing unit and involved in testing of control panel and other electronic equipment.
I’m Professional Electrician at Ghana Energy commission. Sir your teaching is so good, l love it. I wish you all the best.
useful informations,thankyou sir.
thank you about your efforts .
I am an electrical engineer. I want to learn about new methods of compensation for power factor improvements
Capacitors are the best choices as there is no rotating parts.
i am fresher electrical engineer and your work is really mind blowing…….ll read all your articals to improve my knowledge.Thanks a lot for providing all this @free base.
bdw can you have any articals regarding power system buses like Zbus and Ybus and all………? if than plz plz update same……
thanks a lot