Cyber Monday Deal💥

Save 20% with a coupon CYBM20 on PRO Membership Plan and 30% on courses at EEP Academy! Learn from experienced engineers!

# Transformers basics, maintenance and diagnostics

Home / Download Center / Electrical Engineering Books and Technical Guides / Power substation guides / Transformers basics, maintenance and diagnostics

## Transformer Action

Transformer action depends upon magnetic lines of force (flux). At the instant a transformer primary is energized with AC, a flow of electrons (current) begins. During the instant of switch closing, buildup of current and magnetic field occurs.

As current begins the positive portion of the sine wave, lines of magnetic force (flux) develop outward from the coil and continue to expand until the current is at its positive peak. The magnetic field is also at its positive peak. The current sine wave then begins to decrease, crosses zero, and goes negative until it reaches its negative peak.

The magnetic flux switches direction and also reaches its peak in the opposite direction.

With an AC power circuit, the current changes (alternates) continually 60 times per second, which is standard in the United States. Other countries may use other frequencies. In Europe, 50 cycles per second is common.

Strength of a magnetic field depends on the amount of current and number of turns in the winding. When current is reduced, the magnetic field shrinks. When the current is switched off, the magnetic field collapses.

When a coil is placed in an AC circuit, as shown in figure 3, current in the primary coil will be accompanied by a constantly rising and collapsing magnetic field. When another coil is placed within the alternating magnetic field of the first coil, the rising and collapsing flux will induce voltage in the second coil.

When an external circuit is connected to the second coil, the induced voltage in the coil will cause a current in the second coil. The coils are said to be magnetically coupled; they are, however, electrically isolated from each other. Many transformers have separate coils, as shown in figure 3, and contain many turns of wire and a magnetic core, which forms a path for and concentrates the magnetic flux

The winding receiving electrical energy from the source is called the primary winding. The winding which receives energy from the primary winding, via the magnetic field, is called the “secondary” winding.

Either the high- or low-voltage winding can be the primary or the secondary.

With GSUs at Reclamation powerplants, the primary winding is the low voltage side (generator voltage), and the high voltage side is the secondary winding (transmission voltage). Where power is used (i.e., at residences or businesses), the primary winding is the high-voltage side, and the secondary winding is the low-voltage side.

The amount of voltage induced in each turn of the secondary winding will be the same as the voltage across each turn of the primary winding. The total amount of voltage induced will be equal to the sum of the voltages induced in each turn.

Therefore, if the secondary winding has more turns than the primary, a greater voltage will be induced in the secondary; and the transformer is known as a step-up transformer. If the secondary winding has fewer turns than the primary, a lower voltage will be induced in the secondary; and the transformer is a step-down transformer.

Note that the primary is always connected to the source of power, and the secondary is always connected to the load.

In actual practice, the amount of power available from the secondary will be slightly less than the amount supplied to the primary because of losses in the transformer itself. When an AC generator is connected to the primary coil of a transformer (figure 4), electrons flow through the coil due to the generator voltage.

Alternating current varies, and accompanying magnetic flux varies, cutting both transformer coils and inducing voltage in each coil circuit.

The voltage induced in the primary circuit opposes the applied voltage and is known as back voltage or back electro-motive-force (back EMF). When the secondary circuit is open, back EMF, along with the primary circuit resistance, acts to limit the primary current.

Primary current must be sufficient to maintain enough magnetic field to produce the required back EMF.

When the secondary circuit is closed and a load is applied, current appears in the secondary due to induced voltage, resulting from flux created by the primary current. This secondary current sets up a second magnetic field in the transformer in the opposite direction of the primary field.

Thus, the two fields oppose each other and result in a combined magnetic field of less strength than the single field produced by the primary with the secondary open. This reduces the back voltage (back EMF) of the primary and causes the primary current to increase.

The primary current increases until it reestablishes the total magnetic field at its original strength.

In transformers, a balanced condition must always exist between the primary and secondary magnetic fields. Volts times amperes (amps) must also be balanced (be the same) on both primary and secondary.

The required primary voltage and current must be supplied to maintain the transformer losses and secondary load.

 Title: Transformers Basics, Maintenance and Diagnostics – U.S. Department of the Interior Format: PDF Size: 865 KB Pages: 55 Download: Right here | Video Courses | Membership | Download Updates

Cyber Monday Deal 💥 - Save 20% on Pro Membership Plan and 30% on courses at EEP Academy with a coupon CYBM20

1. Alialtaher
Jul 17, 2020

I want a 50 or 100kva transformer that has a two-phase current without a neutral 11kv / 50Hz and a three-phase outward current of 0.4 with a neutral of 50 hz

2. vinoth kumar
Sep 16, 2018

3. horsfall sodieye
Apr 17, 2018

4. Somyot
Jan 13, 2014

Edvard, I am an engineer in this field. So, I think this is the good book for guid line to share with the people in idea “how to take care our transformer for life expansion”. This will be leading to reduce the gobal warming of this world passing the long life of a transformer. However, the file is not complete in the chapter. If you need to share like I said. please give the book in full version to light our knowledge. Finally, the people die everyday but the transfered knowledge is not die from this world. Thank you.

5. praba
Oct 20, 2013

6. frozzty
Feb 25, 2013

Thanks for the documents, is really interesting and explanatory, so perhaps you could upload the missing pages?

Thank you!

• Edvard
Feb 25, 2013

You’re welcome Frozzty, glad you find it usefull! This document is as it is, I cannot add anything to it. Sorry!

• frozzty
Feb 25, 2013

7. amirarya
Feb 25, 2013