Save 15% on Pro Premium Plan with discount code: SX79 (expires on May 31st). Study specialized LV/MV/HV technical articles and papers.

Lightning Protection Risk Assessment Calculator

Home / Download Center / Electrical Software Reviews / Lightning Protection Risk Assessment Calculator

Lightning Risk Assessment Study

Lightning Risk assessment Study is actually the measure of risk of a lightning strike and probability of damages. It assesses the lightening risks to the facility according to international standards requirements.

These calculations are according to IEC Standard 62305-2.

All these calculations are based on:

• lightning strike density in that particular area (provided by OMV i.e. Ng = 8),
• Danger for people,
• Occupation coefficient of structure,
• Relative location of site,
• Fire Risk,
• Associated services,
• Electrical Lines,
• Lightning Protection Level,
• Surge Arrestor and
• Dimensions of installation.

Brief introduction of all are given below.

Lighting Strike Density (Ng)

It is the measure of lightning strikes per kilometre square per year in the particular area.

Higher the lighting strike density, higher the probability of lightning strike which needs higher level of lightning protection level.

Danger for People (h)

It is the factor of presence of people and panic in the building in case of a lightning strike.

 No particular danger 1 Low panic level(<=2 floors, < 100 persons 2 Medium risk of panic (< 1000 persons) 5 Difficult to evacuate (disabled people, hospitals) 5 High risk of panic (> 1000 persons) 10 Hazard for surroundings or environment 20 Contamination of surroundings or environment 50

Occupancy Coefficient (Lf1)

It is the risk reduction factor with respect to theoccupancy of the building / installation. For example, loss due to lighting strike is higher in hospital as compared to a store / warehouse.

 Structure unoccupied 0.1 Structure normally occupied 0.01

Relative Location of Site (Cd)

It is the risk reduction factor with respect to the location and surrounding of the building / installation. For example, chance of lighting strike is minimized if the building is near to a high tower.

 Structure surrounded by higher objects or trees 0.25 Structure surrounded by similar or lower objects 0.5 Isolated structure-No other objects nearby 1 Isolated structure on top of a hill or a hillock 2

Fire Risk (rf)

It is the risk reduction factor with respect to the flammability of the material present in the building / installation.Â For example, in case of lighting strike, loss will be very high at a gas station as compare to the cement store.

 Explosion 1 High 0.1 Ordinary 0.01 Low 0.001

1. Camila
May 05, 2021

I can’t find a course in risk assessment of LPS. Can you help me, please?

2. Rafael Arismendi
Apr 12, 2021

Iâ€™m a Colombian engineer, and I think. Itâ€™s a Good thing you lead us to download the software because the norma is so difficult for your interpretation. I have a worksheet in Excel made by me, but at some points, I look confused.
Thank You.

3. francisco quintero m
Feb 02, 2021

buen dia. donde consigo el software iec Risk assessment ligthing?

4. ALBERTO SALAZAR
Dec 11, 2020

Me podrian enviar el soft evaluacion del riesgo por rayo (IEC Risk assessment ligthing)
Muchas , muchas gracias

5. Damilare
Jun 10, 2020

Great work. Can’t get the software