## The purpose of earthing

System earthing involves the provision of a connection to the general mass of earth. This connection should have a resistance not greater than that required to operate safety mechanisms to isolate the electricity supply from a fault situation.

Second important characteristic of earthing connection is that **it MUST be capable of carrying the maximum expected fault current**.

The value of resistance required might not always be amenable to an automatically set value. Therefore, the various factors which affect the resistance to earth and fault current capacity of the buried conductor, designated the earth electrode, should be considered.

This should include the size and shape of the earth conductor, the resistivity of the soil in which it is buried and the connection of the system to it. It is also essential to consider the current density at the surface of the earth electrode and the ground potentials in its vicinity.

- Nature of site
- Soil resistivity
- Measurement of soil resistivity
- Types of earth electrodes and their resistance calculation

### 1. Nature of site

The basic nature and properties of soil in a given location cannot be changed without considerable expense, and careful consideration of the geology should be used to determine the best location for an earthing system.

**Where there is an option, a site should be chosen in one of the following types of situations in the order of preference given:**

- Wet marshy ground;
- Clay, loamy soil, arable land, clayey soil, clayey soil or loam mixed with small quantities of sand;
- Clay and loam mixed with varying proportions of sand, gravel, and stones;
- Damp and wet sand, peat.

**Dry sand, gravel, chalk, limestone, whinstone, granite, any very stony ground, and all locations where virgin rock is very close to the surface should be avoided if possible.**A site should be chosen where the moisture content is ideally continuously within the range of 15% to 20%. A waterlogged location is not essential unless the soil is sand or gravel.

Care should be taken **to avoid a site where water flows over it (e.g. the bed of a stream) for the beneficial salts can be entirely removed from the soil in such situations**.

#### 1.1 Soil treatment

In high resistivity locations or on rocky ground where long term performance is required, it may be considered necessary to utilize a conductive concrete to improve earth contact resistance around an earth rod or strip (tape) where applicable.

There are commercially available materials to achieve this effectively, but care should be taken **to understand how they work during installation** to ensure that they remain in contact with the rod or strip and do not shrink or swell away after drying out.

Chemical treatment of soil has environmental implicationsand should not be considered as a long term solution in order to meet a specified level of resistance, apart from the risk of corrosion to the earthling system. Coke breeze should also not be used due to its highly corrosive nature.

### 2. Soil resistivity

The resistance to earth of a given electrode depends upon the **electrical resistivity of the soil**. Most first approximation formulae are related to homogenous soil, which is rarely the case in practice, where the different layers of strata will affect the distribution of current passing through the electrode.

Table 1 gives examples of resistivity only. These figures are very general and should not be used to replace actual measurements made at the proposed site. They may be used to give an indication of the difficulties that one might face in preparing an adequate design at the chosen location.

**by the mineral salts in the ground and the level of moisture content**, which is why it should be remembered that readings taken long after installation can vary considerably from the original test results.

Soil temperature has some effect on the upper layers of strata, but is only important under frosty conditions. Therefore any part of an electrode system **which is less that 0.5 m below ground level** should not be considered to be effective.

**Table 1 – Examples of soil resistivity in Ωm**

NOTE! – Table 1 is only to be taken as a **general guide**. Earth resistivity is essentially electrolytic and affected by the moisture content and the soil’s ability to retain moisture plus the chemical composition and concentration of beneficial salts dissolved in the water.

Columns 2 and 3 relate to most of the British Isles, but column 5 is more specific to marshy flats around river estuaries.

### 3. Measurement of soil resistivity

Soil resistivity may be measured in a similar manner to the establishment of the resistance of the earth electrode.

Measurements of the soil resistivity for the pre-determination of the resistance to earth or the impedance to earth should be carried out using a four probe method (widely known as the Wenner method) as follows.

- Drive four equally spaced test electrodes to a depth of
**not greater 5%**of their**spacing apart a**. It is important to ensure that their resistance areas do not overlap (Figure 2) - Pass current between the two outer electrodes
- Measure the earth potential between the two inner electrodes

The resistance R should be taken as the ratio of the voltage between the inner electrodes and the current between the outer electrodes. **In homogenous soil the average resistivity ρ in ohm metres (Ωm) may be taken as:**

ρ = 2 π a R

where:

**a**is the spacing between electrodes, in metres (m);**R**is the resistance measured between the middle electrodes, in ohms (Ω).

The resistivity so determined applies to an electrode separation distance a, which is related to the depth of investigation. By repeating the measurement with increasing values of a, the apparent resistivity involving greater depths may be assessed.

This may be taken as an indication of the possible gain from driving deeper rods, etc., into strata of a lower resistivity to get the required resistance.

#### Few more words on Wenner method…

Four equally spaced test spikes should be driven to a depth of up to **1 m**, the depth not exceeding **5%** of their **separation a**.

It is important to ensure that their resistance areas **do not overlap**. Current should be passed between the two outer electrodes and the **resistance R** may be found as the ratio of the voltage between the inside electrodes to the current conducted through the outside electrodes.

**different values of a**, the average resistivity to various depths may be found and the results indicates whether any advantage is to be gained by installing deeply driven electrodes in order to reach strata of a lower resistivity.

EXAMPLE – If the distance a between electrodes is 1 m the constant for the test setup is calculated as **(2 × 3.14 × 100) cm = 628 cm**. If the instrument reads 40 Ω the earth resistivity is (40 × 628) Ωcm = 25 120 Ωcm.

It should be noted that

environmental conditions such as temperature have an impact on earth resistivitywith a corresponding decrease in resistivity as temperature rises.

### 4. Types of earth electrodes and their resistance calculation

An earthing system should be of the highest integrity and of robust construction to ensure that it remains safe and will not endanger the health and safety of persons or their surroundings. The majority of the formulae presented in this section relate to **low frequency currents** and high frequency examples are not included.

It is therefore important to recognize this issue if a long horizontal tape or bare cable is being considered for producing a low earth resistance, even though the impedance will ultimately be limited to a final value (see Figure 4).

Earthing systems should consist of copper conductors, copper clad or austenitic steel rods of appropriate dimensions, cast iron plates, or steel piles used individually or connected together in combination to form a single local earth electrode system.

The formulae which follow are all based on homogeneous soil conditions, so in most practical situations only give a reasonable idea of the problems (within 15% accuracy) that might exist if the strata is such that the resistivity changes at different levels.

**to apply numerical methods which are more complex than the formulae given below and software is available to carry out the more detailed calculations**. The results from the formulae below are within 10% to 15% accuracy and may be assumed to be sufficient for guidance on what might be the outcome of a given design.

However, onsite resistivity testing should always be carried out prior to carrying out an earth system design and installation.

The effect of shape on an electrode resistance is related to the current density around the particular electrode considered. To obtain a low overall resistance the current density should be as low as possible in the medium surrounding the electrode.

This may be achieved by making the dimensions in one direction large by comparison to the other two. Thus a pipe rod or strip has a much lower resistance than a plate of equal surface area.

#### a) Plates

The approximate resistance to earth of a plate R in ohms (Ω) may be calculated from:

where:

**ρ**is the resistivity of the soil (assumed uniform), in ohm metres (Ωm);**A**is the area of one face of the plate, in square metres (m^{2}).

Plates, if used, should be installed as small units of not greater than **1.2 m × 1.2 m** connected in parallel vertically and at least 2 m apart. The minimum ground cover should not be less than 600 mm and ideally the surrounding soil should be damp.

**Connections to the plate should be by copper conductor, welded, riveted**or otherwise attached with material that will not cause corrosion at the joint. The finished joint should be covered with a heavy coat of bitumen. The connecting strip to the above ground disconnection point should be fully insulated to avoid electrolytic action.

Where the plate is placed in a cut out slot, e.g. in a chalk bed near the surface, the slot should be big enough to allow **at least 300 mm thickness of soil** or other conducting low resistivity medium cover around the whole plate. This requires careful assembly during installation to ensure that the bottom of the plate is resting in the medium used and not on the chalk or high resistivity substrata.

NOTE!For conventional sizes,the resistance is approximately inversely proportional to the linear dimensions, not to the surface area, i.e. a 0.9 m × 0.9 m plate has a resistance approximately 25% higher than a 1.2 m × 1.2 m plate.

#### b) Rod electrode

The resistance of a rod **R _{r}** in ohms (Ω) may be calculated from:

where:

**ρ**is the resistivity of soil, in ohm metres (Ωm);**L**is the length of the electrode, in metres (m);**d**is the diameter of the rod, in metres (m).

NOTE! – Change of diameter has little effect on the overall value of resistance, and the size is more governed by the mechanical strength of the rod to withstand being mechanically driven when deep earth rods are required e.g. to depths of **20 m or more**.

#### c) Parallel connection of aligned rods

The resistance **R _{t}** in ohms (Ω) of

**n**vertically driven rods set

**s**metres apart may be calculated from:

where:

**ρ**is the resistivity of soil, in ohm metres (Ωm);**L**is the length of the electrode, in metres (m);**n**is the number of rods;**s**is the spacing between the rods, in metres (m).

NOTE! – This is based on work carried by Heppe R.J. in 1998 dealing with the computational approach to the potential at the surface face of rods, etc. and gives a slightly more optimistic answer than might be expected.

**the basic theory behind the electrostatic behaviour of an earthing system component**, in effect stating more clearly the interactive effect of the value of s which for practical purposes has long been set as being not less than twice the depth of the rod.

This is related to the hemispherical radius of the rod and that has avoided the effects of using less than the two-times constraint in design thinking. This affects the interference characteristics of multiple rod/tape, etc. systems when the spacing is reduced below the two-times value.

#### d) Strip or round conductor electrodes

This section deals **only with a straight run of conductor**. Other shapes are not covered here.The resistance **R _{ta}** in ohms (Ω) of a strip or round conductor may be calculated from:

where:

**ρ**is the resistivity of soil, in ohm metres (Ωm);**L**is the length of the electrode, in metres (m);**h**is the depth of the electrode, in metres (m);**d**is the diameter of the round conductor or diameter of the equivalent cross sectional area of the strip, in metres (m).

When two or more strips in straight lengths, each of **length L** in meters (m) and a **separation distance s** metres are laid parallel to each other and connected together at one end only the combined resistance may be calculated from the following equation:

R_{n} = F R_{1}

where:

**R**is the resistance of n conductors in parallel, in ohms (Ω)_{n}**R**is the resistance of a single strip of length L, calculated from the preceding Rta equation, in ohms (Ω)._{1}**F has the following value:**- For two lengths: F = 0.5 + [0.078(s/L)] − 0.307
- For three lengths: F = 0.33 + [0.071(s/L)] − 0.408
- For four lengths: F = 0.25 + [0.067(s/L)] − 0.451
- Provided that 0.02 < (s/L) < 0.3

#### e) Mesh

The resistance of a mesh (grid) **R _{m}** ohms (Ω) may be calculated from:

Where:

**ρ**is the resistivity of soil, in ohm metres (Ωm);**A**is the actual area covered by the mesh, in square metres (m^{2});**L**is the total length of strip used in the mesh, in metres (m).

#### f) Resistance of an electrode encased in low resistivity material, e.g. conducting concrete

The resistance of a backfilled electrode **R _{b}** in ohms (Ω) may be calculated from:

where:

**ρ**is the resistivity of soil, in ohm metres (Ωm);**ρ**is the resistivity of the conducting material used for the backfill, in ohm metres (Ωm);_{c}**L**is the length of rod, in metres (m);**d**is the diameter of the rod, in metres (m).

#### g) Miscellaneous electrodes

There are many configurations that can be set out under this heading, but a few of those which one is most likely to try first in order to achieve the required value are included especially when dealing with deep reinforced piles, etc.

- Three rods at the vertices of an equilateral triangle
- Two strips set at right angles to each other meeting at one corner
- Three strips set at 120° meeting at the star point all of equal length
- Four strips set in a cruciform
- Structural steelwork

##### Three rods at the vertices of an equilateral triangle

The resistance **R _{e}** in ohms (Ω) of three interconnected rods set out at the vertices of an equilateral triangle (see Figure 5) of

**side s**metres length may be calculated from:

where:

**ρ**is the resistivity of soil, in ohm metres (Ωm);**L**is the length of rod, in metres (m);**d**is the diameter of rod, in metres (m);**s**is the length of one side of the equilateral triangle, in metres (m).

##### Two strips set at right angles to each other meeting at one corner

The resistance **R _{L}** in ohms (Ω) of two strips of equal length set at 90° with one corner touching (see Figure 6) may be calculated from:

where:

**ρ**is the resistivity of soil, in ohm metres (Ωm);**L**is the total length of strip in metres (m);**h**is the depth of burial in metres (m);**d**is the diameter of the round conductor or diameter of the equivalent cross sectional area of the strip in metres (m).

##### Three strips set at 120° meeting at the star point all of equal length

The resistance **R _{S}** in ohms (Ω) of a star arranged strip (see Figure 7) may be calculated from:

where:

**ρ**is the resistivity of soil, in ohm metres (Ωm); is the total length of strip in metres (m);**L**is the depth of burial in metres (m);**h**is the diameter of the round conductor or diameter of the equivalent cross sectional area of the strip in metres (m).

##### Four strips set in a cruciform

The resistance R_{cr} in ohms (Ω) of four strips set out in a cruciform (see Figure 8) may be calculated from:

**ρ**is the resistivity of soil, in ohm metres (Ωm);**L**is the total length of strip in metres (m);**h**is the depth of burial in metres (m);**d**is the diameter of the round conductor or diameter of the equivalent cross sectional area of the strip in metres (m).

##### Structural steelwork

**Foundation metalwork in concrete** may be used as a ready made and effective earth electrode. The total electrode area formed by the underground metalwork of large structure may often be used to provide an earth resistance lower then that obtainable by other methods.

Overall values well below 1 Ω are obtainable.

It is important that consideration is given to the **possibility of corrosion of the metalwork reinforcement**. The products of corrosion occupy a greater volume than the original metal and cracking might occur. In particular, continuous earth currents should be given attention.

**incompatibility with other buried metalwork**, including other types of earth electrode to which foundation metalwork may be bonded.

NOTE! – It might be necessary to consider the need for **cathodic protection**.

Alternating current should not be expected to cause corrosion, but, rectification sufficient to produce a very small proportion of direct current might take place.

Wherever significant continuous earth leakage current is expected, it is recommended that a main electrode of the types described in previous section be provided to which the foundation electrodes can be bonded to provide auxiliary electrodes, thus giving assistance to high fault currents.

Corrosion of concrete encased steelwork, subject to a.c. fault currents within its carrying capability, may be assumed to be negligible.

NOTE! – Damage to the concrete in the form of cracking, due to arcing or the rapid evaporation of moisture, can occur where the long-term duration earth fault currents exceed the carrying capability of the electrode. This situation is unlikely to arise if the electrode has a resistance sufficiently low to avoid dangerous voltages to earth.

**type of soil, its moisture content, and the design of the foundation.**

Concrete is hygroscopic and, except in dry locations, when buried in soil, it may be expected to have a resistivity of about **30 Ωm to 90 Ωm**, at normal temperatures. This is lower than some types of soil.

It is essential to measure the resistance to earth of any metalwork it is intended to use as an electrode, and to monitor its value at regular intervals afterwards, in order to confirm that it continues to provide an adequate connection to earth.

Ideally confirmation of the combined resistance of all the electrodes should be obtained, but the earth resistance of a structure covering a large area might be quite low and an accurate measurement on a completed structure might be difficult or impossible to achieve.

**to measure the resistance of one footing before it is electrically connected to others**, and before there are any other electrically paralleled footings close by.

If possible, it is advantageous and recommended to measure the resistance of several such footings to gain an indication of the likely variation of resistance.

On the assumption that a representative value of footing resistance can be obtained, the combined effect of all similar footings **R _{TOT}** in ohms (Ω), assumed to be arranged in an approximately rectangular plan, may be determined from the following:

Where:

**R**is the resistance of one footing, in ohms (Ω);_{1}**λ**is the factor from Table 2;

**ρ**is the resistivity of soil, in ohm metres (Ωm);**s**is the spacing of footings, in metres (m);**n**is the number of footings used as electrodes (see the note to Table 2).

NOTE! – This equation is based on assumption that the spacing between adjacent electrodes is such that **the ratio ρ/2πR _{1}s** is less than approximately 0.2.

**Table 2 – Factors for vertical electrodes arranged in a hollow square**

NOTE! – The large proportion of the resistance is due to the concrete to earth is immediately around the metalwork and is dependent on its moisture content. After construction and with the passage of time this moisture content will approach equilibrium with that of the soil, and will usually be dryer than when first laid.

Allowance should be made for the consequent increase in electrode resistance due to changes in moisture content when using measurements made during the installation of a structure.

**to ensure electrical continuity between all metalwork**considered to be part of the electrode.

In the case of contacts between metalwork within concrete or below ground, such as reinforcing bars, this may best be effected by welding. Above ground and at anchor bolts it may generally done by attaching a bond conductor to bypass each structural joint. This applies particularly to surfaces which might have been primed before assembly.

The resistance to earth of a reinforced concrete foundation **R _{r}** in ohms (Ω) may be estimated by assuming that only the vertical reinforcing rods are bonded to the building structure or to the earthing system. The effect of other reinforcement which might be attached by wire ties only, may be neglected.

It may be assumed that the rods are equally spaced in a symmetrical pattern

(see Table 3).

where:

**ρ**is the resistivity of soil, in ohm metres (Ωm);**ρ**is the resistivity of concrete, in ohm metres (Ωm);_{c}**L**is the length of reinforcing rod below ground level, in metres (m);**δ**is the thickness of concrete between rods and soil, in metres (m);**z**is the geometric mean distance of rod cluster, in metres (m).

**Reference //** BS 7430:2011 – Code of practice for protective earthing of electrical installations

rafee

thanks for this information

I have a question:

where is soil resistance in the calculation of Three rods at the vertices of an equilateral triangle formula?

Melvin Surita

This is one of the best design reference i have seen.

Jose M Giménez

Very practical information

yousef farajzadehkhosroshahi

it is useful. Thanks

Florêncio Magina

Excelente informação.

Manish Darji

Valuable information

ahmed messallam

it is valuable information.

thank you