 Study specialized technical articles, papers & courses in low/high voltage fields. Save 50% on all courses at the EEP Academy with the Enterprise Plan.

# Electrical Thumb Rules You MUST Follow (2)

Home / Technical Articles / Electrical Thumb Rules You MUST Follow (2)

Continued from first part: Electrical Thumb Rules You MUST Follow (Part 1)

## Useful Electrical Equations

• For Sinusoidal Current: Form Factor = RMS Value/Average Value = 1.11
• For Sinusoidal Current: Peak Factor = Max Value/RMS Value = 1.414
• Average Value of Sinusoidal Current (Iav) = 0.637 x Im (Im = Max.Value)
• RMS Value of Sinusoidal Current (Irms) = 0.707 x Im (Im = Max.Value)
• A.C Current = D.C Current/0.636.
• Phase Difference between Phase = 360/ No of Phase (1 Phase=230/1=360°, 2 Phase=360/2=180°)
• Short Circuit Level of Cable in KA (Isc) =
(
0.094 x Cable Dia in Sq.mm) /√ Short Circuit Time (Sec)
• Max.Cross Section Area of Earthing Strip (mm2) = √(Fault Current x Fault Current x Operating Time of Disconnected Device ) / K
K = Material Factor, K for Cu = 159, K for Al = 105, K for steel = 58 , K for GI = 80
• Most Economical Voltage at given Distance = 5.5 x √ ((km/1.6) + (kw/100))
• Cable Voltage Drop (%) =
(
1.732 x current x (RcosǾ+jsinǾ) x 1.732 x Length (km) x 100) / (Volt(L-L) x Cable Run.
• Spacing of Conductor in Transmission Line (mm) = 500 + 18 x (P – P Volt) + (2 x (Span in Length)/50).
• Protection radius of Lighnting Arrestor = √h x (2D-h) + (2D+L).
Where h= height of L.A, D-distance of equipment (20, 40, 60 Meter), L=V x t (V=1m/ms, t=Discharge Time).
• Size of Lightning Arrestor = 1.5x Phase to Earth Voltage or 1.5 x (System Voltage/1.732).
• Maximum Voltage of the System = 1.1xRated Voltage (Ex. 66KV = 1.1 × 66 = 72.6KV)
• If Load Factor is 1 or 100% = This is best situation for System and Consumer both.
• If Load Factor is Low (0 or 25%) = you are paying maximum amount of KWH consumption. Load Factor may be increased by switching or use of your Electrical Application.
• Demand Factor = Maximum Demand / Total Connected Load (Demand Factor <1)
• Demand factor should be applied for Group Load
• Diversity Factor =
Sum of Maximum Power Demand / Maximum Demand (Demand Factor >1)
Diversity factor should be consider for individual Load
• Plant Factor (Plant Capacity) = Average Load / Capacity of Plant
• Fusing Factor = Minimum Fusing Current / Current Rating (Fusing Factor>1).
• Voltage Variation (1 to 1.5%) = ((Average Voltage – Min Voltage) x 100)/Average Voltage
Ex: 462V, 463V, 455V, Voltage Variation= ((460 – 455)  x 100)/455 = 1.1%.
• Current Variation (10%) = ((Average Current – Min Current) x 100)/Average Current
Ex: 30A,35A,30A, Current Variation = ((35-31.7) x 100)/31.7 = 10.4%
• Fault Level at TC Secondary
= TC (VA) x 100 / Transformer Secondary (V) x Impedance (%)
• Motor Full Load Current = Kw /1.732 x KV x P.F x Efficiency

Get access to premium HV/MV/LV technical articles, electrical engineering guides, research studies and much more! It helps you to shape up your technical skills in your everyday life as an electrical engineer. ### Jignesh Parmar

Jignesh Parmar has completed M.Tech (Power System Control), B.E (Electrical). He is member of Institution of Engineers (MIE), India. He has more than 20 years experience in transmission & distribution-energy theft detection and maintenance electrical projects.

1. Swapnendu Sil
May 04, 2016

Hi Sir,
I want to know what cable or wire can be used for 32 amp industrial sockets

• Ali
Feb 07, 2018

For single phase you can use 3core 6sqmm cable or for 3phase you can use 5core 6 sqmm cable

2. surinderjit singh
Aug 14, 2015

Dear Sir
please let me know a lightening Arrestor fixed on a building of 50 Feet height and height of lightening Arrestor is 10 feet , how much area it will cover for protection purpose.
regards
surinderjit

3. Hasmukh Patel
Jul 06, 2015

Really very good knowledge, that helps to know even very difficult to find solution.

4. deshmukh V.
Sep 12, 2014

thanks for ‘useful’ information.

5. Rajan.K
Jul 28, 2014

The thumb rules are really great. thanks a lot for providing such information in a capsule

6. NITIN
May 30, 2014

Size of Lightning Arrestor = 1.5x Phase to Earth Voltage or 1.5 x (System Voltage/1.732)
MEANS WHAT SIZE OF THAT ARRESTER ???

7. PARAG NIKUMBH
Dec 16, 2013

8. aakifnouman
Sep 02, 2013

A.C Current = D.C Current/0.636

what is 0.636??

9. sumitfloyd
Sep 02, 2013

A.C Current = D.C Current/0.636.
Please clarify this relation on how do you get it?