Save 50% on all EEP Academy courses with Enterprise Membership Plan and study specialized LV/MV/HV technical articles & guides.

# Learn how to interpret interlocking schemes between MV cubicles (single line and wiring diagrams)

Home / Technical Articles / Learn how to interpret interlocking schemes between MV cubicles (single line and wiring diagrams)

## MV switchgear & control issues

There are numerous variations of MV switchgear topology, measurement, and control logic. However, there are also some basic rules related to these aspects which may be frequently seen in practice, with the purpose of increased safety and reliability during operation. Within this article, the real example of MV switchgear with two main busbar sections will be described.

Most of the attention will be given to concrete practical solutions related to some control issues. This subject will be illustrated by use of adequate single line and wiring diagrams.

## Example of MV switchgear

Switchgear which is the subject of this example is installed inside MV/LV substation and serving as the power supply of new factory of construction steel products. There are eight MV/LV power transformers in total, with a rated power of 3.5 MVA each.

Table 1 – Main technical characteristics of MV switchgear

 Construction: Metal enclosed Installation type: Indoor Isolation type: Air insulated (isolation medium inside cubicles) Protection degree: IP 3X Ambient temperature: −5 … +40 °C Number of cubicles: 14 Rated voltage: 24 kV (*) Operating voltage: 20 kV (*) Rated lightning withstand voltage: 125 kV, 1.2/50 µs Rated power frequency withstand voltage: 50 kV, 1 min. Rated current of main busbars: 1250 A Rated short time withstand current: 20 kA × 2 s Rated peak withstand current: 50 kA Arc test current: 21 kA × 1 s (**) Internal arc classification (IAC): AFLR (**) Rated voltage of control and signal circuits: 110 VDC

(*) Rated voltage of the switchgear is the upper limit of phase to phase RMS value which switchgear is capable to withstand continuously. Operating voltage is rated (expected) phase to phase value during operation. This value is usually allowed to vary within ±10% limits or less.

For MV applications, rated voltage of the switchgear is 20% greater than rated operating voltage. Values of lightning and power frequency withstand voltage are also related to these values, according to IEC standard.

(**) IAC parameter defines from which sides MV switchgear is safely accessible during internal fault followed by presence of electric arc. This parameter depends on arc test current value, dimensions of room inside of which MV switchgear is installed, and technical measures taken for dissipation of heat and pressure caused by arc.

This technical article/guide requires a Premium Membership. You can choose an annually based Plus, Pro, or Enterprise membership plan. Subscribe and enjoy studying specialized technical articles, online video courses, electrical engineering guides, and papers. With EEP’s premium membership, you get additional essence that enhances your knowledge and experience in low- medium- and high-voltage engineering fields.

Check out each plan’s benefits and choose the membership plan that works best for you or your organization.

Did you know?Save 50% on all video courses by purchasing Enterprise plan.