Limited Time Offer: Save 15% on Pro Plan with discount coupon: MX15. Study specialized LV/MV/HV technical articles and studies.

# Electrical Design Calculations For Industrial Plants

Home / Premium Content / Advanced Electrical Engineering Guides / Electrical Design Calculations For Industrial Plants

## Line Design

In order to design the line there are few important elements to define: voltage drop, the load, sizing the cable, ampacity, and cable temperature. The load is based on the motor. Ampacity is that which is adequate for the rms value of the motor current profile plus the fast transient spike.

Choosing cable temperature includes the choice of ambient temperature for the line design.

The load is the current profile summarized in the motor electrical analysis. It is repeated here. The peak current is 1062 A, which lasts for 6 min. This is followed by 24 min with a current of 220 A. This cycle is repeated for 10 h/day.
The rms value of this current profile is:

(1,062)2 × (6 min) = 6,767,064

(220)2 × (24 min) = 1,161,600 / 7,928,664

Dividing this sum by 30 min yields the mean square, or 264,289 A2. The rms value is the square root, or 514 A. This is an rms load of:

(480) × (514) × (1.732) × 10-3 = 427kVA

Note that the 514 A value slightly exceeds the motor’s current, 421 A, when operating at 400 Hp and 460 V. But it doesn’t exceed the motor current, 547 A, when operating at 90% voltage and 80°C rise.

This technical article/guide requires a Premium Membership. You can choose an annually based Plus, Pro, or Enterprise membership plan. Subscribe and enjoy studying specialized technical articles, online video courses, electrical engineering guides, and papers. With EEP’s premium membership, you get additional essence that enhances your knowledge and experience in low- medium- and high-voltage engineering fields.

Check out each plan’s benefits and choose the membership plan that works best for you or your organization.

Limited time offer 💥 – Save 15% on Pro Membership Plan with discount coupon MX15