MV Switchgear Control Circuits
Control circuits are vital to the operation of medium voltage switchgear. The integrity of these control circuits is essential to the switchgear’s proper operation, so commissioning and maintenance activities records are extremely important for troubleshooting practices. Furthermore, one has to comprehend the reading and interpretations of the control circuits in order to develop the skills of troubleshooting and sequence of operation follow.
Although the control circuits are many, they boil down to the circuit breaker close/trip coils irrespective of the many details involved.
The good news is that the principles addressed in this technical article apply to almost all types of switchgear with some exceptions. The control circuits for Gas Insulated Substation (GIS), for example, are much more detailed and complicated, but they have many common principles with 13.8 kV switchgear.
Hence, it is extremely important to master the skills of control circuit interpretation for better and faster troubleshooting activities.
In addition, a brief view of busbar arrangements utilized in different applications is introduced, as it has a direct effect on the interlocking contacts that might be used in the control circuits. The next article will talk about substation single-line diagram, circuit breaker tripping circuit, bay-control-protection-unit (BCPU) and alarm circuits, indication circuits, and mechanical/electrical interlocking circuits.
- Busbar Arrangement Overview
- Switchgear Components
- Substation Single-Line Diagram
- Substation Control Systems
- About My Next Article (Trip Coils, Control/Alarm Circuits, Interlocking Schemes)