Save 50% on all courses at the EEP Academy with the Enterprise Plan and study specialized technical articles, papers & video courses.

# Calculation of short-circuit withstand current rating for low voltage switchgear

Home / Download Center / Electrical Engineering Books and Technical Guides / Electrical engineering guides / Calculation of short-circuit withstand current rating for low voltage switchgear

## Short-circuit current rating (SCCR)

Short-circuit current rating (SCCR) is the maximum short-circuit current a component or assembly can safely withstand when protected by a specific overcurrent protective device(s) or for a specified time. Short-circuit current ratings provide the level of fault current that a component or a piece of equipment can safely withstand (based on a fire and shock hazard external to the enclosure).

Without knowing the available fault current and short-circuit current rating, it is impossible to determine if components or equipment can be safely installed.

Individual panel components have an SCCR or interrupting rating. The component with the lowest SCCR in the panel limits the overall panel assembly rating. This SCCR rating has to be displayed on the nameplate and is usually calculated by the manufacturer or assembler of the control panel.

The short-circuit current magnitude is determined either by computation or by measurement. For new applications, the measurement cannot be done before preparation of the switchgear, nor is it always possible to relay on measurement of older installations.

The manufacturer often does not know the switchgears future operating conditions (feeding transformer, type and length of cable network, change of conductor resistance caused by the temperature change, additional power to the grid, caused by motors, etc.)

It is the responsibility of the consulting or electrical design engineer to verify that all industrial control panels are applied in a manner such that the panelâ€™s SCCR is greater than the systemâ€™s available fault current.

It is the responsibility of the industrial control panel manufacturer to provide accurate SCCR information to the consulting engineer and authority having jurisdiction through required labels and published technical information.

### Determining the rated short-time withstand current (Icw) of a circuit of an assembly

The original manufacturer of the switchgear system, is responsible for the verification of the short circuit withstand capacity of the system components, e.g. the Icw value of the busbars.

Rated short-circuit withstand current is determined by the values Ik“, Icw, Icp, Icu. A verification of the short-circuit withstand strength is not required for the following:

1. Assemblies having a rated short-time withstand current or rated conditional short-circuit current not exceeding 10 kA r.m.s.
2. Assemblies protected by current-limiting devices having a cut-off current not exceeding 17 kA at the maximum allowable prospective short-circuit current at the terminals of the incoming circuit of the assemblies.
3. Auxiliary circuits of assemblies intended to be connected to transformers whose rated power does not exceed 10 kVA for a rated secondary voltage of not less than 110 V, or 1,6 kVA for a rated secondary voltage less than 110 V, and whose short-circuit impedance is not less than 4%.

All other circuits shall be verified.â€ť (IEC61439-1, 2009, p. 73)

The example based on the network in the Figure above shows how to determine the short-time withstand current Icw.

 Title: Short-circuit withstand current rating for low voltage switchgear – Thesis for Bachelor’s Degree of Matthias Christian SchĂĽtt at Savonia University Of Applied Sciences Format: PDF Size: 15.2 MB Pages: 75 Download: Here » Register First | Video Courses | Download Updates

Get access to premium HV/MV/LV technical articles, advanced electrical engineering guides, papers, and much more! It will help you to shape up your technical skills in your everyday life as an electrical engineer.

1. rajesh chauhan
Mar 22, 2022

Short Circuit withstand capacity and duration for Armour (k.Amps)

2. Hani Zakar
Dec 24, 2020

hi
how to calculate the short circuit current of amore than one Generator connected on a busbar
is the (SCCR) will be the sum of the (SCCR) of the generators or what?

3. RABBANI
Oct 14, 2020

this is really helpful website. the books are free for downloads. personally from this website i have cleared many doubts and understand the concepts.

4. Wisdom Ezeifedikwa
Feb 07, 2020

I am really interested in knowing how to calculate the short circuit withstand current rating. (SCCR)