Why energy efficient? Let’s see.
Many energy saving actions can encourage specifiers and engineers to look closely at the savings which can be made by specifying an energy efficient version of a particular component.
1. The Motor
As an example, consider a ventilation fan motor, working full time, at 100 metres from the distribution panel.
Rating kW  % Load  Output Power kW  Duty hours/year 
7.5  87  6.525  8,760 
Typical Motor parameters:
Efficiency  Output Power  Input Power  Annual Consumption  Current per phase  
Comparison  [%]  [kW]  [kW]  [kWh]  [A] 
Standard  87  6.525  7.50  65,700  9.84 
Energy efficient  90  6.525  7.25  63,510  9.51 
The input power is given by the following formula:
At a unit cost of £0.0443 per unit, the annual saving is £97.02, while the incremental cost of the energyefficient motor would be about £95.
Go back to energy efficient options ↑
The Cable
A conductor crosssection of 1.5 mm^{2} would be considered adequate – from a thermal rating point of view – to carry this current (< 10A). Such a cable would have a resistance of 25 milliohms per metre.
The power loss in the cable is:
p_{L} = I^{2} × R
The reduction in power loss in the cable due to the use of an energy efficient motor is:
p_{D} = (I_{1}^{2} – I_{2}^{2}) × R
p_{D} = (9.842 – 9.512) × 25 × 10^{3} × 100
p_{D} = 5.796 × 2.5 = 14.49 W
Energy saved per year = 127 kWh
For a 1.5 mm^{2} cable supplying an energy efficient motor the power loss is:
= 9.51^{2} × 25 × 10^{3} x 100 = 226.1 W per phase, or 678.3 W total for all three phases.
Using, say, 10 mm^{2} cable would reduce the total loss to 103.1 W, giving an annual saving of
575.2 × 8,760 = 5,037 kWh
At a unit price of £0.0443 per unit, the annual saving would be £223.14. Since the cost of installation will not be significantly higher than for the smaller cable, the only additional cost is the purchase cost of the cable.
This table shows the power saving achieved so far:
For 6.525 kW output power  Standard motor  Energy efficient motor 
1.5 mm^{2} cable [kW]  10 mm^{2} cable [kW]  
Input power  8.178  7.353 
Overall efficiency [%]  80  89 
The overall annual power saving is 7,227 kWh, or £320.16.
Go back to energy efficient options ↑
3. The Transformer
There are dozen of factors which should be considered when selecting local transformers (core losses, load losses, winding material, etc.). By careful selection of the motor and cabling we have already reduced the input power by 10%, and consequently the attributable transformer load loss by 21%.
Using the standard and low loss transformers from Table 1 and assuming that it is running at 80% load, the incremental loss associated with a 1 kW load for each transformer can be estimated at 24.4 W and 21.25 W respectively.
Typical RES (10% TDR) 
Typical Industry user  Typical RES (5% TDR) 

Loss capitalisation values per kilowatt  £3,000/£625  £3,988/£814  £3,750/£780 
Standard loss alternative  
Noload loss 0.735 kW  £2,205.00  £2,931.18  £2,756.25 
Load loss 4.8 kW  £3,000.00  £3,907.20  £3,744.00 
Price  £5,000.00  £5,000.00  £5,000.00 
Totals  £10,205.50  £11,838.38  £11,500.25 
Low loss alternative  
Noload loss 0.38 kW  £1,140.00  £1,515.44  £1,425.00 
Load loss 4.08 kW  £2,550.00  £3,321.12  £3,182.40 
Price  £6,690.00  £6,690.00  £6,690.00 
Totals  £10,380.00  £11,526.56  £11,297.40 
Amorphous steel alternative  
Noload loss 0.145 kW  £435.00  £578.26  £543.75 
Load loss 4.77 kW  £2,981.25  £3,882.78  £3,720.60 
Price  £7,315.00  £7,315.00  £7,315.00 
Totals  £10,731.25  £11,776.04  £11,579.35 
TDR – Test discount rate
REC – Regional Electricity Companies
For the incremental load of the motor, the additional losses are 195.2 W for the standard and 170 W for the low loss transformer, so that the low loss transformer saves a further 221 kWh per annum. The additional cost of selecting a low loss transformer is equivalent to £5.37 per kW of rating (based on a 315 kW unit), so that attributable to the motor load (remembering that the overall loading is 80%) is £53.60.
Input power [kW]  
For 6.525 kW output power  Standard motor 1.5 mm^{2} cable standard transformer (kW) 
Energy efficient motor 10 mm^{2} cable low loss transformer (kW) 
Input power to motor  7.500  7.250 
Input power to cable  8.178  7.353 
– plus incremental transformer loss  8.373  7.523 
Annual consumption  73,347 kWh  65,901 kWh 
The overall saving is 7,446 kWh per year, equivalent to £329.85 per year (at £0.0443 per unit).
It must be remembered that the selection of more efficient downstream components, including cabling, reduces losses in other components upstream.
Go back to energy efficient options ↑
Reference // Electrical Energy Efficiency by Copper Development Association
AMIT KUMAR
Its nothing about specification parameters of the equipment. Its general theory and calculations with low loss and related results. If possible please try to provide some information if standard and energy efficient equipment are manufactured by the manufacturer or if there is any standard code (national or international) providing difference for them.