Limited Time Offer: Save 15% on Pro Plan with discount coupon: MX15. Study specialized LV/MV/HV technical articles and studies.

# Sizing of 110V DC charger for MV panels – Auxiliary power supply in power substations

Home / Technical Articles / Sizing of 110V DC charger for MV panels – Auxiliary power supply in power substations

## Auxiliary DC power system

An auxiliary DC power system that consists of a charger, battery bank, DC distribution system, and monitoring system is a critical part of the primary/secondary substation. It is directly associated with the mechanism of fault detection, trip coil operation, remote operation, etc. This article focuses on the primary aspects of optimal sizing of 110V DC charger and power supply system for a typical MV power distribution substation.

Usually, the auxiliary DC supply used in power substations operates in 110V or 220V, barring some exceptions. To design the complete auxiliary DC supply system for a substation, the design engineer must go through multiple calculations and contemplations.

Through this article, the readers can get an idea to design and put together a complete 110V auxiliary DC supply system for a typical MV power distribution substation by considering multiple factors like- the sizing of the battery bank, calculation of DC loads, rating of battery charger, size and rating of DC distribution panel, etc.

### 1. Introducing a typical 110 V DC auxiliary power supply of a substation

The DC auxiliary power supply is required in a substation to ensure that the critical equipment remains in operation continuously even while the primary AC supply is interrupted. When a circuit breaker opens to interrupt the power supply in a radial feeder, this leads to interruption of the power supply to the circuit breaker itself.

Thus, the breaker can no longer be closed electrically unless an auxiliary power supply is available that ensures that the breaker can still operate when the main power supply is interrupted.

For this, the battery bank stores the energy with the help of an appropriate charger and supplies the DC loads continuously or during power failure via the DC distribution system under proper monitoring and control as per requirement.

Figure 1 – Block diagram of DC system

Go back to Contents Table ↑

### 2. Major factors for determining the battery size

The sizing of the battery bank and an overall DC auxiliary power supply system rely upon various factors. Basically, under normal operation, the charger feeds the DC power to the battery to recover the battery voltage after a discharge while also compensating for any self-discharge losses in the battery. The battery charger also feeds any continuous load on the auxiliary DC system, while the battery storage primarily supports the intermittent loads like trip coils, motors, etc.

The battery size calculation assumes the worst-case scenario in which the battery has to drive the continuous and intermittent load both, caused by charger failure.

This technical article/guide requires a Premium Membership. You can choose an annually based Plus, Pro, or Enterprise membership plan. Subscribe and enjoy studying specialized technical articles, online video courses, electrical engineering guides, and papers. With EEP’s premium membership, you get additional essence that enhances your knowledge and experience in low- medium- and high-voltage engineering fields.

Check out each plan’s benefits and choose the membership plan that works best for you or your organization.

Limited time offer 💥 – Save 15% on Pro Membership Plan with discount coupon MX15