Save 50% on all Video Courses with Enterprise Membership Plan and study specialized LV/MV/HV technical articles and guides.

# A case study of fault level calculations for a MV/LV network using direct method

Home / Technical Articles / A case study of fault level calculations for a MV/LV network using direct method

## Step-by-step fault level calculations

This technical article represents the case study of fault level calculations for an MV/LV network using the direct method. There are many advantages of the direct approach, and the main of them is that it directly uses the system single line diagram, equipment data, and basic electrical equations.

It’s worth mentioning that the direct method of fault level calculations is more straightforward to comprehend than the per-unit method.

For a start, it’s important to prepare a single line diagram of the electrical power supply and distribution network, clearly indicating all the significant network elements (power supply sources, transformers, electric motors, etc.), fault current contributors, short circuit protective devices, etc.

Let’s now describe the network components for which we will calculate the fault levels:

1. The 11kV incoming terminals (source fault current)
2. The auxiliary transformer’s 11kV terminals
3. The 6.6kV switchgear bus
4. The service transformer’s 6.6kV terminals
5. The 415V PCC panel bus
6. The 415V MCC panel bus
7. Motor contribution (510kW motor, PF=0.8; eff=85%) at the 6.6kV switchgear bus, assuming that:
1. Only one motor in operation
2. Both motors in operation
8. Motor contribution (110kW motors; IrM = 193.23A) at the 415V PCC panel, assuming five such motors are in operation.

Since an article is quite long, it is divided into four parts. The first part will deal with the calculation of resistances, reactances, and impedances on various network points through fifteen steps. The second part is a table where all these values are nicely summarized. The third part presents a summary of fault current calculation formulae and its value for each of the six network points explained above.

Finally, the fourth part of this article investigates the motor contribution to the overall fault at the 6.6kV switchgear bus and the LV PCC bus.

This technical article/guide requires a Premium Membership. You can choose an annually based Plus, Pro, or Enterprise membership plan. Subscribe and enjoy studying specialized technical articles, online video courses, electrical engineering guides, and papers. With EEP’s premium membership, you get additional essence that enhances your knowledge and experience in low- medium- and high-voltage engineering fields.

Check out each plan’s benefits and choose the membership plan that works best for you or your organization.

Good to know 💥Get 50% discount on all video courses by purchasing Enterprise plan.